Inverter compressor

Short description: Air conditioning technology

In air conditioning, an inverter compressor is a compressor that is operated with an inverter.

In the hermetic type, it can either be a scroll or reciprocating compressor. This type of compressor uses a drive to control the compressor motor speed to modulate cooling capacity. Capacity modulation is a way to match cooling capacity to cooling demand to application requirements.

The first inverter air conditioners were released in 1980-1981.[1][2]

## Contents

* 1 Market needs for variable capacity
* 2 Working principle
* 3 Applications
* 4 Challenges in adopting inverter scroll in HVAC systems
* 5 See also
* 6 References
* 7 External links

## Market needs for variable capacity

Typical load profile in a building

Many refrigeration and air conditioning systems require reliable processes which are more efficient, compact, environmentally friendly, and easy to install and maintain. The cooling requirements vary over a wide range during the day and over the year due to ambient conditions, occupancy and use, lighting, etc.

* In comfort cooling, there may also be the need for a stable and accurate temperature and humidity control in areas such as hospitals, IT & telecoms, process cooling. In applications such as schools, restaurants and office buildings, it is important that the cooling system is able to adapt to wide daily shifts in load.
* In process applications such as fermentation, growing tunnels and industrial processes, accurate temperature settings are required to secure production quality.

## Working principle

The variable-frequency drive controls the speed of compressor motor. The compressor is specifically designed to run at different motor speeds to modulate cooling output. Variable speed operation requires an appropriate compressor for full speed operation and a special compressor lubrication system. Proper oil management is a critical requirement to ensure compressor lifetime. Proper oil management provides proper lubrication for scroll set at low speed and prevents excess oil from being injected into the circuit when operating at full speed.

## Applications

Variable speed technology can be implemented in HVACR, close control and process cooling applications and as diverse as packaged or split air-conditioning units, rooftops, chillers, precision cooling, VRF and condensing units.

Rooftop
This is a very common unit type. The rising cost of energy means that air conditioning manufacturers must develop a new generation of high-efficiency, cost-effective air conditioners for commercial buildings that meet or exceed a part-load efficiency standard of typically 18 IEER. The aim is to reduce energy use by 30% over current equipment. Inverter technology helps OEMs to build units which meet this demand.
Air handling units
These have integrated cooling and are used in commercial applications for air conditioning and humidity control in diverse ranges of buildings such as small office buildings, fitness and medical centres. Inverter compressor solutions enable smooth modulation and huge energy savings.
Modular chillers
A typical modular chiller installation uses multiple fixed-speed. These units share the same water system to supply the building with cooled or heated water. Hybrid tandem, associating one inverter and one fixed-speed compressor, can better match the capacity requirement compared to a modular chiller with fixed-speed tandem compressors and increases efficiency.
Solar-powered air conditioning
Inverter compressors make solar-powered air conditioning viable. Before, fixed-speed on/off compressors required an inrush, or surge, current that was 4 to 6 times greater than the running current at startup, meaning a requirement of 4 to 6 times more solar panels or batteries. Inverter compressors start slowly and avoid this startup power which is needed each time a standard on/off compressor comes on.
Modular chillers
A typical modular chiller installation uses multiple fixed-speed. These units share the same water system to supply the building with cooled or heated water. Hybrid tandem, associating one inverter and one fixed-speed compressor, can better match the capacity requirement compared to a modular chiller with fixed-speed tandem compressors and increases efficiency.
Close control units
These are used in the cooling of IT and electronic equipment used in data centres, telecommunications and in manufacturing industries. Power management, energy consumption and heat loads are major challenges. Maintenance of a stable temperature and humidity control, compactness of the system and overall efficiency are key design challenges in these applications for ensuring data safety and availability. This is where inverter technology makes the difference.
Process cooling
In many industries the machinery and processes generate a large amount of heat which requires cooling, to protect the equipment and / or to ensure that the product being manufactured is of the required quality. Inverter technology helps to secure the process while providing greater efficiency.
Variable refrigerant flow (VRF)
VRF units are very popular cooling or reversible systems (heating and cooling). They combine the flexibility for building owners and occupants alike, with energy efficiency, high comfort, and ease of installation, without compromising on reliability. VRF systems already extensively use inverter technology.[3]

## Challenges in adopting inverter scroll in HVAC systems

The compressor and drive need to be qualified to work together and for dedicated applications. The drive modulates the compressor speed and prevents it from operating out of the compressor operating limits. The inverter frequency drives need to use algorithms developed specifically for heating, ventilation and air conditioning (HVAC) or for refrigeration. They ensure that the system will run within the application constraints. The drive can also manage other devices such as oil injection valves or multiple compressors. As the compressor rotational speed changes, the amount of refrigerant — and oil — flowing through the compressor increases or decreases. The drive ensures that the compressor and bearings are optimally lubricated at all compressor speeds.

## See also

* Variable refrigerant flow

## References

1. ↑ http://www.ieee-jp.org/japancouncil/jchc/adm/milestone/39Inverter_Air_Conditioners.pdf
2. ↑ https://ethw.org/w/images/8/8b/IEEE_Milestone_Leaflet_ENG.PDF
3. ↑ "HVAC Systems that Support Your Design Vision". https://www.architectmagazine.com/technology/products/hvac-systems-that-support-your-design-vision.

## External links

* Why and how we use capacity control
* Compressors efficiently evolve with time

* v
* t
* e

Heating, ventilation, and air conditioning

Fundamental concepts|

* Air changes per hour
* Bake-out
* Building envelope
* Convection
* Dilution
* Domestic energy consumption
* Enthalpy
* Fluid dynamics
* Gas compressor
* Heat pump and refrigeration cycle
* Heat transfer
* Humidity
* Infiltration
* Latent heat
* Noise control
* Outgassing
* Particulates
* Psychrometrics
* Sensible heat
* Stack effect
* Thermal comfort
* Thermal destratification
* Thermal mass
* Thermodynamics
* Vapour pressure of water

Technology|

* Absorption refrigerator
* Air barrier
* Air conditioning
* Antifreeze
* Automobile air conditioning
* Autonomous building
* Building insulation materials
* Central heating
* Central solar heating
* Chilled beam
* Chilled water
* Constant air volume (CAV)
* Coolant
* Dedicated outdoor air system (DOAS)
* Deep water source cooling
* Demand-controlled ventilation (DCV)
* Displacement ventilation
* District cooling
* District heating
* Electric heating
* Energy recovery ventilation (ERV)
* Firestop
* Forced-air
* Forced-air gas
* Free cooling
* Heat recovery ventilation (HRV)
* Hybrid heat
* Hydronics
* HVAC
* Ice storage air conditioning
* Kitchen ventilation
* Mixed-mode ventilation
* Microgeneration
* Natural ventilation
* Passive cooling
* Passive house
* Radiant heating and cooling system
* Radiant cooling
* Radiant heating
* Radon mitigation
* Refrigeration
* Renewable heat
* Room air distribution
* Solar air heat
* Solar combisystem
* Solar cooling
* Solar heating
* Thermal insulation
* Underfloor air distribution
* Underfloor heating
* Vapor barrier
* Vapor-compression refrigeration (VCRS)
* Variable air volume (VAV)
* Variable refrigerant flow (VRF)
* Ventilation

Components|

* Air conditioner inverter
* Air door
* Air filter
* Air handler
* Air ionizer
* Air-mixing plenum
* Air purifier
* Air source heat pumps
* Automatic balancing valve
* Back boiler
* Barrier pipe
* Blast damper
* Boiler
* Centrifugal fan
* Ceramic heater
* Chiller
* Condensate pump
* Condenser
* Condensing boiler
* Convection heater
* Compressor
* Cooling tower
* Damper
* Dehumidifier
* Duct
* Economizer
* Electrostatic precipitator
* Evaporative cooler
* Evaporator
* Exhaust hood
* Expansion tank
* Fan coil unit
* Fan filter unit
* Fan heater
* Fire damper
* Fireplace
* Fireplace insert
* Freeze stat
* Flue
* Freon
* Fume hood
* Furnace
* Furnace room
* Gas compressor
* Gas heater
* Gasoline heater
* Geothermal heat pump
* Grease duct
* Grille
* Ground-coupled heat exchanger
* Heat exchanger
* Heat pipe
* Heat pump
* Heating film
* Heating system
* High efficiency glandless circulating pump
* High-efficiency particulate air (HEPA)
* High pressure cut off switch
* Humidifier
* Infrared heater
* Inverter compressor
* Kerosene heater
* Louver
* Mechanical fan
* Mechanical room
* Oil heater
* Packaged terminal air conditioner
* Plenum space
* Pressurisation ductwork
* Process duct work
* Radiator
* Radiator reflector
* Recuperator
* Refrigerant
* Register
* Reversing valve
* Run-around coil
* Scroll compressor
* Solar chimney
* Solar-assisted heat pump
* Space heater
* Smoke exhaust ductwork
* Thermal expansion valve
* Thermal wheel
* Thermosiphon
* Thermostatic radiator valve
* Trickle vent
* Trombe wall
* Turning vanes
* Ultra-low particulate air (ULPA)
* Whole-house fan
* Windcatcher
* Wood-burning stove

Measurement
and control|

* Air flow meter
* Aquastat
* BACnet
* Blower door
* Building automation
* Carbon dioxide sensor
* Clean Air Delivery Rate (CADR)
* Gas sensor
* Home energy monitor
* Humidistat
* HVAC control system
* Intelligent buildings
* LonWorks
* Minimum efficiency reporting value (MERV)
* OpenTherm
* Programmable communicating thermostat
* Programmable thermostat
* Psychrometrics
* Room temperature
* Smart thermostat
* Thermostat
* Thermostatic radiator valve

Professions, trades,
and services|

* Architectural acoustics
* Architectural engineering
* Architectural technologist
* Building services engineering
* Building information modeling (BIM)
* Deep energy retrofit
* Duct leakage testing
* Environmental engineering
* Hydronic balancing
* Kitchen exhaust cleaning
* Mechanical engineering
* Mechanical, electrical, and plumbing
* Mold growth, assessment, and remediation
* Refrigerant reclamation
* Testing, adjusting, balancing

Industry organizations|

* ACCA
* AHRI
* AMCA
* ASHRAE
* ASTM International
* BRE
* BSRIA
* CIBSE
* Institute of Refrigeration
* IIR
* LEED
* SMACNA

Health and safety|

* Indoor air quality (IAQ)
* Passive smoking
* Sick building syndrome (SBS)
* Volatile organic compound (VOC)

See also|

* ASHRAE Handbook
* Building science
* Fireproofing
* Glossary of HVAC terms
* World Refrigeration Day

* Template:Home automation
* Template:Solar energy

0.00

(0 votes)

|

Retrieved from "https://handwiki.org/wiki/index.php?title=Engineering:Inverter_compressor&oldid=3894876"
*[v]: View this template
*[t]: Discuss this template
*[e]: Edit this template