Lighting control system

Short description: Intelligent network based lighting control

Las Vegas Convention Center Loop showing effects of lighting control system

A lighting control system is intelligent network-based lighting control that incorporates communication between various system inputs and outputs related to lighting control with the use of one or more central computing devices. Lighting control systems are widely used on both indoor and outdoor lighting of commercial, industrial, and residential spaces. Lighting control systems are sometimes referred to under the term smart lighting. Lighting control systems serve to provide the right amount of light where and when it is needed.[1]

Lighting control systems are employed to maximize the energy savings from the lighting system, satisfy building codes, or comply with green building and energy conservation programs. Lighting control systems may include a lighting technology designed for energy efficiency, convenience and security. This may include high efficiency fixtures and automated controls that make adjustments based on conditions such as occupancy or daylight availability. Lighting is the deliberate application of light to achieve some aesthetic or practical effect (e.g. illumination of a security breach). It includes task lighting, accent lighting, and general lighting.

## Contents

* 1 Lighting controls
* 1.1 Advantages
* 1.2 Minimizing energy usage
* 1.3 Convenience
* 1.4 Security
* 2 Automated control
* 2.1 Chronological time
* 2.2 Solar time
* 2.3 Occupancy
* 2.3.1 Ultrasonic
* 2.4 Daylight availability
* 2.4.1 Daylight sensing
* 2.5 Alarm conditions
* 2.6 Program logic
* 2.7 Automatic dimming
* 2.8 Use of sensors
* 2.8.1 Components
* 2.8.2 Others
* 3 Standards and protocols
* 3.1 Bluetooth lighting control
* 3.2 Smart lighting ecosystem
* 3.3 Information transmitting with smart light
* 4 Theatrical lighting control
* 5 Smart-lighting emergency ballast for fluorescent lamps
* 5.1 Overview
* 6 Advances in photonics
* 7 Notable inventors
* 8 See also
* 9 References

## Lighting controls

The term lighting controls is typically used to indicate stand-alone control of the lighting within a space. This may include occupancy sensors, timeclocks, and photocells that are hard-wired to control fixed groups of lights independently. Adjustment occurs manually at each devices location. The efficiency of and market for residential lighting controls has been characterized by the Consortium for Energy Efficiency.[2]

The term lighting control system refers to an intelligent networked system of devices related to lighting control. These devices may include relays, occupancy sensors, photocells, light control switches or touchscreens, and signals from other building systems (such as fire alarm or HVAC). Adjustment of the system occurs both at device locations and at central computer locations via software programs or other interface devices.

### Advantages

The major advantage of a lighting control system over stand-alone lighting controls or conventional manual switching is the ability to control individual lights or groups of lights from a single user interface device. This ability to control multiple light sources from a user device allows complex lighting scenes to be created. A room may have multiple scenes pre-set, each one created for different activities in the room. A major benefit of lighting control systems is reduced energy consumption. Longer lamp life is also gained when dimming and switching off lights when not in use. Wireless lighting control systems provide additional benefits including reduced installation costs and increased flexibility over where switches and sensors may be placed.[3]

### Minimizing energy usage

Lighting applications represents 19% of the world's energy use and 6% of all greenhouse emissions.[4] In the United States, 65 percent of energy consumption is used by commercial and industrial sectors, and 22 percent of this is used for lighting.

Smart lighting enables households and users to remotely control cooling, heating, lighting and appliances, minimizing unnecessary light and energy use. This ability saves energy and provides a level of comfort and convenience. From outside the traditional lighting industry, the future success of lighting will require involvement of a number of stakeholders and stakeholder communities. The concept of smart lighting also involves utilizing natural light from the sun to reduce the use of man-made lighting, and the simple concept of people turning off lighting when they leave a room.[5]

### Convenience

A smart lighting system can ensure that dark areas are illuminated when in use. The lights actively respond to the activities of the occupants based on sensors and intelligence (logic) that anticipates the lighting needs of an occupant. This can enhance comfort, improve safety, reduce manual effort, and improve energy efficiency.

### Security

Lights can be used to dissuade those from areas they should not be. A security breach, for example, is an event that could trigger floodlights at the breach point. Preventative measures include illuminating key access points (such as walkways) at night and automatically adjusting the lighting when a household is away to make it appear as though there are occupants.

## Automated control

Lighting control systems typically provide the ability to automatically adjust a lighting device's output based on:

* Chronological time (time of day)
* Solar time (sunrise/sunset)
* Occupancy using occupancy sensors
* Daylight availability using photocells
* Alarm conditions
* Program logic (combination of events)

### Chronological time

Chronological time schedules incorporate specific times of the day, week, month or year.

### Solar time

Solar time schedules incorporate sunrise and sunset times, often used to switch outdoor lighting. Solar time scheduling requires that the location of the building be set. This is accomplished using the building's geographic location via either latitude and longitude or by picking the nearest city in a given database giving the approximate location and corresponding solar times.

### Occupancy

Space occupancy is primarily determined with occupancy sensors. Smart lighting that utilizes occupancy sensors can work in unison with other lighting connected to the same network to adjust lighting per various conditions.[6] The table below shows potential electricity savings from using occupancy sensors to control lighting in various types of spaces.[7]

#### Ultrasonic

The advantages of ultrasonic devices are that they are sensitive to all types of motion and generally there are zero coverage gaps, since they can detect movements not within the line of sight.[8][7]

### Daylight availability

Electric lighting energy use can be adjusted by automatically dimming and/or switching electric lights in response to the level of available daylight. Reducing the amount of electric lighting used when daylight is available is known as daylight harvesting.

#### Daylight sensing

In response to daylighting technology, daylight-linked automated response systems have been developed to further reduce energy consumption.[9][10] These technologies are helpful, but they do have their downfalls. Many times, rapid and frequent switching of the lights on and off can occur, particularly during unstable weather conditions or when daylight levels are changing around the switching illuminance. Not only does this disturb occupants, it can also reduce lamp life. A variation of this technology is the 'differential switching' or 'dead-band' photoelectric control which has multiple illuminances it switches from to reduce occupants being disturbed.[11][12]

### Alarm conditions

Alarm conditions typically include inputs from other building systems such as the fire alarm or HVAC system, which may trigger an emergency 'all lights on' or ' all lights flashing' command for example.

### Program logic

Program logic can tie all of the above elements together using constructs such as if-then-else statements and logical operators. Digital Addressable Lighting Interface (DALI) is specified in the IEC 62386 standard.

### Automatic dimming

The use of automatic light dimming is an aspect of smart lighting that serves to reduce energy consumption.[13] Manual light dimming also has the same effect of reducing energy use.

### Use of sensors

In the paper "Energy savings due to occupancy sensors and personal controls: a pilot field study", Galasiu, A.D. and Newsham, G.R have confirmed that automatic lighting systems including occupancy sensors and individual (personal) controls are suitable for open-plan office environments and can save a significant amount of energy (about 32%) when compared to a conventional lighting system, even when the installed lighting power density of the automatic lighting system is ~50% higher than that of the conventional system.[14]

#### Components

A complete sensor consists of a motion detector, an electronic control unit, and a controllable switch/relay. The detector senses motion and determines whether there are occupants in the space.[9] It also has a timer that signals the electronic control unit after a set period of inactivity. The control unit uses this signal to activate the switch/relay to turn equipment on or off. For lighting applications, there are three main sensor types: passive infrared, ultrasonic,[8] and hybrid.

#### Others

Motion-detecting (microwave), heating-sensing (infrared), and sound-sensing; optical cameras, infrared motion, optical trip wires, door contact sensors, thermal cameras, micro radars, daylight sensors.[15]

## Standards and protocols

In the 1980s there was a strong requirement to make commercial lighting more controllable so that it could become more energy efficient. Initially this was done with analog control, allowing fluorescent ballasts and dimmers to be controlled from a central source. This was a step in the right direction, but cabling was complicated and therefore not cost effective.

Tridonic was an early company to go digital with their broadcast protocols, DSI, in 1991. DSI was a basic protocol as it transmitted one control value to change the brightness of all the fixtures attached to the line. What made this protocol more attractive, and able to compete with the established analog option, was the simple wiring.

There are two types of lighting control systems which are:

* Analog lighting control
* Digital lighting control

Examples for analog lighting control systems are:

* 0-10V based system.
* AMX192 based systems (often referred to as AMX) (USA standard).
* D54 based systems (European standard).

In production lighting 0-10V system was replaced by analog multiplexed systems such as D54 and AMX192, which themselves have been almost completely replaced by DMX512. For dimmable fluorescent lamps (where it operates instead at 1-10 V, where 1 V is minimum and 0 V is off) the system is being replaced by DSI, which itself is in the process of being replaced by DALI.

Examples for digital lighting control systems are:

* DALI based system.
* DSI based system
* KNX based systems

Those are all wired lighting control systems.

There are also wireless lighting control systems that are based on some standard protocols like MIDI, ZigBee, Bluetooth Mesh, and others. The standard for digital addressable lighting interface, mostly in professional and commercial deployments, is IEC 62386-104. This standard specifies the underlying technologies, which in wireless are VEmesh, which operates in the industrial Sub-1 GHz frequency band and Bluetooth Mesh, which operates in the 2.4 GHz frequency band.[16]

Other notable protocols, standards and systems include:

* Architecture for Control Networks
* Art-Net
* Bluetooth mesh Lighting model
* C-Bus
* Dynalite
* INSTEON
* Lonworks
* MIDI
* Modbus
* RDM
* VSCP
* X10
* Z-Wave

### Bluetooth lighting control

The new type of control for lighting system is using Bluetooth connection directly to the lighting system. It is recently introduced by Philips HUE and company new name as Signify formerly known as Philips Lighting. This system will need a smartphone or tablet where the user can install a special Philips Hue Bluetooth app. The Bluetooth bulbs don't need a Philips Hue bridge to function. There is no need to have a Wi-Fi or data connection for controlling the lights with that system.

### Smart lighting ecosystem

Smart lighting systems can be controlled using the internet to adjust lighting brightness and schedules.[6] One technology involves a smart lighting network that assigns IP addresses to light bulbs.[17]

### Information transmitting with smart light

Schubert predicts that revolutionary lighting systems will provide an entirely new means of sensing and broadcasting information. By blinking far too rapidly for any human to notice, the light will pick up data from sensors and carry it from room to room, reporting such information as the location of every person within a high-security building. A major focus of the Future Chips Constellation is smart lighting, a revolutionary new field in photonics based on efficient light sources that are fully tunable in terms of such factors as spectral content, emission pattern, polarization, color temperature, and intensity. Schubert, who leads the group, says smart lighting will not only offer better, more efficient illumination; it will provide "totally new functionalities."

## Theatrical lighting control

Architectural lighting control systems can integrate with a theater's on-off and dimmer controls, and are often used for house lights and stage lighting, and can include worklights, rehearsal lighting, and lobby lighting. Control stations can be placed in several locations in the building and range in complexity from single buttons that bring up preset options-looks, to in-wall or desktop LCD touchscreen consoles. Much of the technology is related to residential and commercial lighting control systems.

The benefit of architectural lighting control systems in the theater is the ability for theater staff to turn worklights and house lights on and off without having to use a lighting control console. Alternately, the light designer can control these same lights with light cues from the lighting control console so that, for instance, the transition from houselights being up before a show starts and the first light cue of the show is controlled by one system.

## Smart-lighting emergency ballast for fluorescent lamps

The function of a traditional emergency lighting system is the supply of a minimum illuminating level when a line voltage failure appears. Therefore, emergency lighting systems have to store energy in a battery module to supply lamps in case of failure. In this kind of lighting systems the internal damages, for example battery overcharging, damaged lamps and starting circuit failure must be detected and repaired by specialist workers.

For this reason, the smart lighting prototype can check its functional state every fourteen days and dump the result into a LED display. With these features they can test themselves checking their functional state and displaying their internal damages. Also the maintenance cost can be decreased.[18]

### Overview

The main idea is the substitution of the simple line voltage sensing block that appears in the traditional systems by a more complex one based on a microcontroller. This new circuit will assume the functions of line voltage sensing and inverter activation, by one side, and the supervision of all the system: lamp and battery state, battery charging, external communications, correct operation of the power stage, etc., by the other side.

The system has a great flexibility, for instance, it would be possible the communication of several devices with a master computer, which would know the state of each device all the time.

A new emergency lighting system based on an intelligent module has been developed. The micro-controller as a control and supervision device guarantees increase in the installation security and a maintenance cost saving.

Another important advantage is the cost saving for mass production specially whether a microcontroller with the program in ROM memory is used.

## Advances in photonics

The advances achieved in photonics are already transforming society just as electronics revolutionized the world in recent decades and it will continue to contribute more in the future. From the statistics, North America's optoelectronics market grew to more than $20 billion in 2003. The LED (light-emitting diode) market is expected to reach $5 billion in 2007, and the solid-state lighting market is predicted to be $50 billion in 15–20 years, as stated by E. Fred Schubert,[19] Wellfleet Senior Distinguished Professor of the Future Chips Constellation at Rensselaer.

## Notable inventors

* Alexander Nikolayevich Lodygin – carbon-rod filament incandescent lamp (1874)[20]
* Joseph Swan – carbonized-thread filament incandescent lamp (1878)[21]
* Thomas Edison – long-lasting incandescent lamp with high-resistance filament (1880)[21]
* John Richardson Wigham – electric lighthouse illumination (1885)[22]
* Nick Holonyak – light-emitting diode (1962)[23]
* Howard Borden, Gerald Pighini, Mohamed Atalla, Monsanto – LED lamp (1968)[24][25]
* Shuji Nakamura, Isamu Akasaki, Hiroshi Amano – blue LED (1992)[26]

## See also

* Banning of incandescent light bulbs
* Dimmer
* Home automation
* Lutron
* Light fixture
* Light in school buildings
* Light pollution
* Lighting for the elderly
* Lighting control console
* Luminous efficacy
* Over-illumination
* Passive infrared sensor
* Seasonal affective disorder
* Stage lighting
* Street lighting
* Sustainable lighting
* Three-point lighting, technique used in both still photography and in film
* Ultrasonic sensors

Lists

* List of light sources
* Timeline of lighting technology

## References

1. ↑ DiLouie, Craig (2008). Lighting controls handbook. Lilburn, Ga. [u.a.]: Fairmont Press [u.a.]. pp. 239. ISBN 978-1-4200-6921-1.
2. ↑ "CEE Residential Lighting Controls Market Characterization". Consortium for Energy Efficiency. http://library.cee1.org/content/cee-residential-lighting-controls-market-characterization. Retrieved 2014-08-11.
3. ↑ "Lighting control saves money and makes sense". Daintree Networks. http://www.daintree.net/downloads/whitepapers/smart-lighting.pdf. Retrieved 2009-06-19.
4. ↑ Bahga, Arshdeep; Madisetti, Vijay (2014-08-09) (in en). Internet of Things: A Hands-On Approach. VPT. pp. 50. ISBN 978-0-9960255-1-5. https://books.google.com/books?id=JPKGBAAAQBAJ&pg=PA50.
5. ↑ Khanna 2014, pp. 475-476.
6. ↑ 6.0 6.1 Bahga, A.; Madisetti, V. (2014). Internet of Things: A Hands-On Approach. Vpt. p. 50. ISBN 978-0-9960255-1-5. https://books.google.com/books?id=JPKGBAAAQBAJ&pg=PA50. Retrieved February 10, 2015.
7. ↑ 7.0 7.1 The energy observer, Energy Efficiency Information for the Facility Manager, Quarterly Issue – December 2007, Occupancy Sensors for Lighting Control
8. ↑ 8.0 8.1 Khanna 2014, p. 480.
9. ↑ 9.0 9.1 Khanna 2014, p. 476.
10. ↑ Khanna 2014, pp. 482-484.
11. ↑ Li D, Cheung K, Wong S, Lam T. An analysis of energy-efficient light fittings and lighting controls. Applied Energy. February 2010;87(2):558-567, Academic Search Premier, Ipswich, MA.
12. ↑ Hung-Liang C, Yung-Hsin H. Design and Implementation of Dimmable Electronic Ballast for Fluorescent Lamps Based on Power-Dependent Lamp Model. IEEE Transactions on Plasma Science. July 2010;38(7):1644-1650, Academic Search Premier, Ipswich, M
13. ↑ Khanna 2014, p. 478.
14. ↑ Galasiu, A.D.; Newsham, G.R., Energy savings due to occupancy sensors and personal controls: a pilot field study, Lux Europa 2009, 11th European Lighting Conference, Istanbul, Turkey, September 9–11, 2009, pp. 745-752
15. ↑ "Already Efficient, LED Lights Get Smarter". Martin LaMonica. http://www.technologyreview.com/view/513786/already-efficient-led-lights-get-smarter/.
16. ↑ "Virtual Extension | Technology" (in en-US). https://virtual-extension.com/products/technology/.
17. ↑ "An Internet Address for Every Light Bulb :: NXP Semiconductors". 2011-05-16. http://www.nxp.com/news/press-releases/2011/05/an-internet-address-for-every-light-bulb.html.
18. ↑ J. M. Alonso, J. Diaz, C. Blanco, M. Rico, A Smart-Lighting Emergency Ballast for Fluorescent Lamps Based on Microcontroller
19. ↑ "Rensselaer Magazine: Winter 2004: Looking Into Light (Page 2)". rpi.edu. http://www.rpi.edu/magazine/winter2004/feature2-pg2.html.
20. ↑ Edison Electric Light Co. <gwmw class="ginger-module-highlighter-mistake-type-1" id="gwmw-15801507026460266671638">vs.</gwmw> United States Electric Lighting Co., Federal Reporter, F1, Vol. 47, 1891, p. 457.
21. ↑ 21.0 21.1 Guarnieri, M. (2015). "Switching the Light: From Chemical to Electrical". IEEE Industrial Electronics Magazine 9 (3): 44–47. doi:10.1109/MIE.2015.2454038. https://www.research.unipd.it/bitstream/11577/3164116/5/21 LightElectric.pdf.
22. ↑ "John Richardson Wigham 1829–1906". BEAM (Commissioners of Irish Lights) 35: 21–22. 2006. http://www.commissionersofirishlights.com/media/35546/Beam_2006.PDF#page=23.
23. ↑ "Inventor of Long-Lasting, Low-Heat Light Source Awarded $500,000 Lemelson-MIT Prize for Invention". Massachusetts Institute of Technology. Washington, D.C.. April 21, 2004. http://web.mit.edu/invent/n-pressreleases/n-press-04LMP.html.
24. ↑ Andrews, David L. (2015). Photonics, Volume 3: Photonics Technology and Instrumentation. John Wiley & Sons. p. 2. ISBN 9781118225547. https://books.google.com/books?id=mkqVBgAAQBAJ&pg=PA2.
25. ↑ Borden, Howard C.; Pighini, Gerald P. (February 1969). "Solid-State Displays". Hewlett-Packard Journal: 2–12. http://hparchive.com/Journals/HPJ-1969-02.pdf.
26. ↑ "The Nobel Prize in Physics 2014". Nobel Prize. https://www.nobelprize.org/prizes/physics/2014/press-release/.

* v
* t
* e

Home automation

System|

| Elements|

* Actuators
* Hardware controllers
* Sensors

|

Interconnection
type|

| Wired|

* Cable (xDSL)
* Optical fiber
* Powerline
* PLCBUS
* Universal powerline bus (UPB)
* X10

|

Wireless|

* Radio frequency
* Bluetooth
* Bluetooth Low Energy
* DECT
* EnOcean
* GPRS
* MyriaNed
* One-Net
* UMTS
* Wi-Fi
* Zigbee
* Z-Wave
* Infrared (Consumer IR)

Both|

* Insteon
* KNX

Network
technologies,
by function|

| Device
interconnection|

* Bluetooth
* Bluetooth Low Energy
* FireWire
* IrDA
* USB
* Zigbee

|

Control and
automation|

* AllJoyn
* Bus SCS with OpenWebNet
* C-Bus (protocol)
* CEBus
* EnOcean
* EHS
* Insteon
* Luxom
* KNX
* LonWorks
* One-Net
* Universal powerline bus
* X10
* Zigbee
* Z-Wave

Data
networking|

* Ethernet
* HomePlug
* HomePNA
* Wi-Fi

Tasks|

* Audio and video
* Heating, ventilation and air conditioning
* Lighting control system
* Other systems
* Robotics
* Security
* Thermostat automation

Other|

* Costs
* Mesh networking
* Organizations
* Smart grid

See also
Home of the future
Building automation
Floor plan
Home automation
Home energy monitor
Home network
Home server
House navigation system
INTEGER Millennium House
The House of the Future
Ubiquitous computing
Xanadu Houses

0.00

(0 votes)

Original source: https://en.wikipedia.org/wiki/Lighting control system. Read more

|

Retrieved from "https://handwiki.org/wiki/index.php?title=Earth:Lighting_control_system&oldid=4120557"
*[v]: View this template
*[t]: Discuss this template
*[e]: Edit this template