Safety curtain

Short description: Fire safety precaution at theatres

For the 1918 film, see The Safety Curtain.

This article has multiple issues. Please help improve it or discuss these issues on the talk page. (Learn how and when to remove these template messages)

This article relies too much on references to primary sources. Please improve this by adding secondary or tertiary sources. (May 2007) (Learn how and when to remove this template message)

|

(Learn how and when to remove this template message)

Safety curtain of St Martin's Theatre in London. The lever and weights used to operate a fire curtain as seen from a theatre's backstage

A safety curtain (or fire curtain in America) is a passive fire protection feature used in large proscenium theatres. It is usually a heavy fabric curtain located immediately behind the proscenium arch. Asbestos-based materials were originally used to manufacture the curtain, before the dangers of asbestos were widely known. The safety curtain is sometimes referred to as an iron curtain (or iron) in British theatres, regardless of the actual construction material.

Occupational safety and health regulations state that the safety curtain must be able to resist fire for a short time to delay fires starting on stage from spreading to the auditorium and the rest of the theatre, to provide additional exiting time for audience members and members of staff.

The curtain is heavy and requires its own dedicated operating mechanisms. In an emergency, the stage manager can usually pull a lever backstage which will cause the curtain to fall rapidly into position. Alternatively, heat-sensitive components can be built into the rigging to automatically close the curtain in case of fire. It may be released electronically with the activation of the building's fire alarm system. It can also be flown in and out, as regulations in some jurisdictions state that it must be shown to the audience, to prove its effective operation, for a certain amount of time during every performance.[citation needed]

A safety curtain is required per United States building codes if the proscenium wall is required to be fire rated.[1] The curtain is required to demonstrate a fire rating of approximately 30 min per testing.[2]

In the UK, it is a requirement that a safety curtain must be fully down within the proscenium opening within 30 seconds of being released.[3]

In 1794 the Theatre Royal, Drury Lane became the first theatre to install an iron safety curtain.[4] Several other serious fires, including the 1887 Exeter Theatre Royal fire, led to the introduction of safety curtains on a wider scale. However, Edinburgh's Royal Lyceum Theatre, built in 1883, has also been described as the "[first] theatre in Britain to be fitted with an iron safety curtain".[5][6]

File:Eiserner Vorhang des Kölner Opernhauses - Testbetrieb.webm A very early example of a safety curtain installation in the United States was at the New Fifth Avenue Theatre (New York City) which opened in 1873.[7] Chicago's 1903 Iroquois Theatre fire resulted in over 600 deaths when the theater's safety curtain got stuck midway down, along with other structural deficiencies in the building.[8]

## Related stage fire safety devices

The safety curtain can be combined with other safety devices, such as:

* Smoke pockets \- are steel channels located at either side of the proscenium arch that the safety curtain travels within to create a physical barrier between the auditorium and the stage. The safety curtain is not intended to create an air seal but rather prevent material from falling from the stage house into the audience.
* Fire doors \- that automatically close any doorway onto the stage in the event of a fire.
* Smoke vents \- vents above the stage which will allow smoke to move out of the roof of the theatre, enabling safer evacuation of the audience.
* Water curtain \- sprinkler heads or other nozzles directly in front of the proscenium to prevent sparks from flying off the stage or to extinguish any burning material (such as a set) which may fall through the proscenium.

## References

1. ↑ 2021 International Building Code, 410.2.5
2. ↑ NFPA 80 Standard for Fire Doors and Other Opening Protectives, 2.1.14
3. ↑ (in English) BS 9999. BSI Standards Publication. 2017. pp. 303. ISBN 978 0 580 97716 9.
4. ↑ "History of theatres: Eighteenth-century theatre". The Theatres Trust. http://www.theatrestrust.org.uk/resources/exploring-theatres/history-of-theatres/eighteenth-century-theatre. Retrieved April 22, 2017.
5. ↑ Bruce., Peter (1999). Scotlandʼs splendid theatres : architecture and social history from the Reformation to the present day. Polygon. ISBN 0-7486-6261-8. OCLC 44184624. http://worldcat.org/oclc/44184624.
6. ↑ "GRINDLAY STREET, ROYAL LYCEUM THEATRE (LB30031)". http://portal.historicenvironment.scot/designation/LB30031.
7. ↑ "A NEW THEATRE.: Mr. Daly's Twenty-eighth Street Enterprise". New York Times. 16 November 1873. https://www.nytimes.com/1873/11/16/archives/a-new-theatre-mr-dalys-twentyeighth-street-enterprise.html.
8. ↑ "Nineteen Chicago Theatres Closed, Iroquois Theatre Employee Charged with Manslaughter". New York Times. 2 January 1904. https://www.nytimes.com/1904/01/02/archives/nineteen-chicago-theatres-closed-mayor-harrison-takes-steps-to.html.

## External links

* Berufsgenossenschaft Regulation: Accident-Prevention Regulation BGV-C1, for Staging and Production Facilities for the Entertainment Industry, adopted on 1 April 1998 (PDF, 266 KB)
* Safety Curtains: Types and Models
* Fire Safety in the Theater

* v
* t
* e

Fire protection

General|

* Active fire protection
* Passive fire protection

Fire suppression|

| Manual|

* Fire blanket
* Fire bucket
* Fire extinguisher

|

Automatic|

* Condensed aerosol fire suppression
* Fire sprinkler system
* Fire sprinkler
* Gaseous fire suppression

Detection|

* Flame detector
* Heat detector
* Smoke detector

Notification|

* Drill
* Fire alarm system
* Call box
* Control panel
* Notification appliance
* Pull station/call point
* Smoke detector

Awards|

* Arthur B. Guise Medal
* Harry C. Bigglestone Award

* Category
* Commons

0.00

(0 votes)

Original source: https://en.wikipedia.org/wiki/Safety curtain. Read more

|

Retrieved from "https://handwiki.org/wiki/index.php?title=Engineering:Safety_curtain&oldid=3896776"
*[v]: View this template
*[t]: Discuss this template
*[e]: Edit this template