Linear compressor

Short description: Gas compressor where the piston is driven by a linear actuator

A linear compressor is a gas compressor where the piston moves along a linear track to minimize friction and reduce energy loss during conversion of motion. This technology has been successfully used in cryogenic applications which must be oil-less. The suspension spring can be flexure type or coil type. An oil-free valved linear compressor enables the design of compact heat exchangers.[1] Linear compressors work similarly to a solenoid: by using a spring-loaded piston with an electromagnet connected to AC through a diode. The spring-loaded piston is the only moving part, and it is placed in the center of the electromagnet. During the positive cycle of the AC, the diode allows energy to pass through the electromagnet, generating a magnetic field that moves the piston backwards, compressing the spring, and generating suction. During the negative cycle of the AC, the diode blocks current flow to the electromagnet, letting the spring uncompress, moving the piston forward, and compressing the refrigerant. The compressed refrigerant is then released by a valve.

## Contents

* 1 History
* 2 Valved linear compressor
* 3 See also
* 4 References
* 5 External links

## History

A number of patents for linear compressors powered by free-piston engines were issued in the 20th century, including:

* To Brown, Boveri & Cie, GB191215963, published 1913-10-08[2]
* To Hugo Junkers, CA245708, published 1924-12-30[2]
* To Raúl Pateras Pescara, US1615133, published 1927-01-18[2]

The first market introduction of a linear compressor to compress refrigerant in a refrigerator was in 2001.[3]

## Valved linear compressor

The single piston linear compressor uses dynamic counterbalancing, where an auxiliary movable mass is flexibly attached to a movable piston assembly and to the stationary compressor casing using auxiliary mechanical springs with zero vibration export at minimum electrical power and current consumed by the motor.[4] It is used in cryogenics.[4] Linear compressors are used as they have fewer mechanical losses.[5]

Linear compressors are made by LG and used in LG and Kenmore refrigerators. Linear compressors were also announced by Embraco.[6][7] Compressors of this type have less noise, and are more energy efficient than conventional refrigerator compressors. The Embraco linear compressors are also claimed to be oil-free. In the 2010s and 2020s, multiple lawsuits in the United States alleged that the LG compressors had a high rate of failure or lack of expected cooling. As of 2024, there were settlements[8] and ongoing cases.[9]

## See also

* Physics:Booster pump
* Physics:Hydrogen compressor - Device to increase pressure of hydrogen gas
* Chemistry:Liquid hydrogen - Liquid state of the element hydrogen
* Engineering:Timeline of low-temperature technology - Aspect of history
* Physics:Timeline of hydrogen technologies - None
* Scroll compressor

## References

1. ↑ Liang, Kun (2017). "A review of linear compressors for refrigeration". International Journal of Refrigeration 84: 253–273. doi:10.1016/j.ijrefrig.2017.08.015. http://sro.sussex.ac.uk/id/eprint/69918/1/Linear Compressor Review Accepted Version.pdf.
2. ↑ 2.0 2.1 2.2 "Espacenet : Original document". http://worldwide.espacenet.com/publicationDetails/originalDocument?CC=GB&NR=191215963A&KC=A&FT=D&ND=3&date=19131008&DB=EPODOC&locale=en_EP. Retrieved 5 November 2017.
3. ↑ "Problems 4.7 - A Home Refrigerator with a Sunpower Linear Compressor". https://people.ohio.edu/urieli/thermo/Intro/Chapt.1_6/refrigerator/refrig_problems.html. Retrieved 5 November 2017.
4. ↑ 4.0 4.1 Reed, Jaime; Dadd, Mike; Bailey, Paul; Petach, Michael; Raab, Jeff (2005). "Development of a valved linear compressor for a satellite borne J–T cryocooler". Cryogenics 45 (7): 496–500. doi:10.1016/j.cryogenics.2005.03.007. Bibcode: 2005Cryo...45..496R.
5. ↑ "Linear compressor". https://patents.google.com/patent/US8496453B2/en.
6. ↑ "Oil-less linear compressor launched". 2014-03-20. https://www.coolingpost.com/world-news/oil-less-linear-compressor-launched/.
7. ↑ "Embraco claims oil-less compressor breakthrough". https://www.acr-news.com/embraco-claims-oil-less-compressor-breakthrough.
8. ↑ Wroclawski, Daniel (2020-09-17). "LG Settles Class-Action Lawsuit Over Refrigerator Compressors". https://www.consumerreports.org/lawsuits-settlements/lg-settles-class-action-lawsuit-over-refrigerator-compressors/.
9. ↑ Roher, Christine; Johnson, Carolyn (2023-12-19). "People say pricey refrigerator compressors are conking out within a few years, sometimes just months" (in en-US). https://www.nbclosangeles.com/investigations/lg-refrigerator-compressor-lawsuit-appliances/3293828/.

## External links

* Blain, Loz (2021-11-03). "Super-efficient linear compressor could vastly reduce air con power use" (in en-US). https://newatlas.com/energy/magtor-efficient-compressor-energy-efficient/.
* Aloha ben (2025-08-29) the LG Linear Compressor. "detailed instructions on diagnosing and testing the linear-compressor unit in LG refrigerators". Alabam. Retrieved 2025-08-30.

* v
* t
* e

Heating, ventilation, and air conditioning

Fundamental concepts|

* Air changes per hour
* Bake-out
* Building envelope
* Convection
* Dilution
* Domestic energy consumption
* Enthalpy
* Fluid dynamics
* Gas compressor
* Heat pump and refrigeration cycle
* Heat transfer
* Humidity
* Infiltration
* Latent heat
* Noise control
* Outgassing
* Particulates
* Psychrometrics
* Sensible heat
* Stack effect
* Thermal comfort
* Thermal destratification
* Thermal mass
* Thermodynamics
* Vapour pressure of water

Technology|

* Absorption refrigerator
* Air barrier
* Air conditioning
* Antifreeze
* Automobile air conditioning
* Autonomous building
* Building insulation materials
* Central heating
* Central solar heating
* Chilled beam
* Chilled water
* Constant air volume (CAV)
* Coolant
* Dedicated outdoor air system (DOAS)
* Deep water source cooling
* Demand-controlled ventilation (DCV)
* Displacement ventilation
* District cooling
* District heating
* Electric heating
* Energy recovery ventilation (ERV)
* Firestop
* Forced-air
* Forced-air gas
* Free cooling
* Heat recovery ventilation (HRV)
* Hybrid heat
* Hydronics
* HVAC
* Ice storage air conditioning
* Kitchen ventilation
* Mixed-mode ventilation
* Microgeneration
* Natural ventilation
* Passive cooling
* Passive house
* Radiant heating and cooling system
* Radiant cooling
* Radiant heating
* Radon mitigation
* Refrigeration
* Renewable heat
* Room air distribution
* Solar air heat
* Solar combisystem
* Solar cooling
* Solar heating
* Thermal insulation
* Underfloor air distribution
* Underfloor heating
* Vapor barrier
* Vapor-compression refrigeration (VCRS)
* Variable air volume (VAV)
* Variable refrigerant flow (VRF)
* Ventilation

Components|

* Air conditioner inverter
* Air door
* Air filter
* Air handler
* Air ionizer
* Air-mixing plenum
* Air purifier
* Air source heat pumps
* Automatic balancing valve
* Back boiler
* Barrier pipe
* Blast damper
* Boiler
* Centrifugal fan
* Ceramic heater
* Chiller
* Condensate pump
* Condenser
* Condensing boiler
* Convection heater
* Compressor
* Cooling tower
* Damper
* Dehumidifier
* Duct
* Economizer
* Electrostatic precipitator
* Evaporative cooler
* Evaporator
* Exhaust hood
* Expansion tank
* Fan coil unit
* Fan filter unit
* Fan heater
* Fire damper
* Fireplace
* Fireplace insert
* Freeze stat
* Flue
* Freon
* Fume hood
* Furnace
* Furnace room
* Gas compressor
* Gas heater
* Gasoline heater
* Geothermal heat pump
* Grease duct
* Grille
* Ground-coupled heat exchanger
* Heat exchanger
* Heat pipe
* Heat pump
* Heating film
* Heating system
* High efficiency glandless circulating pump
* High-efficiency particulate air (HEPA)
* High pressure cut off switch
* Humidifier
* Infrared heater
* Inverter compressor
* Kerosene heater
* Louver
* Mechanical fan
* Mechanical room
* Oil heater
* Packaged terminal air conditioner
* Plenum space
* Pressurisation ductwork
* Process duct work
* Radiator
* Radiator reflector
* Recuperator
* Refrigerant
* Register
* Reversing valve
* Run-around coil
* Scroll compressor
* Solar chimney
* Solar-assisted heat pump
* Space heater
* Smoke exhaust ductwork
* Thermal expansion valve
* Thermal wheel
* Thermosiphon
* Thermostatic radiator valve
* Trickle vent
* Trombe wall
* Turning vanes
* Ultra-low particulate air (ULPA)
* Whole-house fan
* Windcatcher
* Wood-burning stove

Measurement
and control|

* Air flow meter
* Aquastat
* BACnet
* Blower door
* Building automation
* Carbon dioxide sensor
* Clean Air Delivery Rate (CADR)
* Gas sensor
* Home energy monitor
* Humidistat
* HVAC control system
* Intelligent buildings
* LonWorks
* Minimum efficiency reporting value (MERV)
* OpenTherm
* Programmable communicating thermostat
* Programmable thermostat
* Psychrometrics
* Room temperature
* Smart thermostat
* Thermostat
* Thermostatic radiator valve

Professions, trades,
and services|

* Architectural acoustics
* Architectural engineering
* Architectural technologist
* Building services engineering
* Building information modeling (BIM)
* Deep energy retrofit
* Duct leakage testing
* Environmental engineering
* Hydronic balancing
* Kitchen exhaust cleaning
* Mechanical engineering
* Mechanical, electrical, and plumbing
* Mold growth, assessment, and remediation
* Refrigerant reclamation
* Testing, adjusting, balancing

Industry organizations|

* ACCA
* AHRI
* AMCA
* ASHRAE
* ASTM International
* BRE
* BSRIA
* CIBSE
* Institute of Refrigeration
* IIR
* LEED
* SMACNA

Health and safety|

* Indoor air quality (IAQ)
* Passive smoking
* Sick building syndrome (SBS)
* Volatile organic compound (VOC)

See also|

* ASHRAE Handbook
* Building science
* Fireproofing
* Glossary of HVAC terms
* World Refrigeration Day

* Template:Home automation
* Template:Solar energy

0.00

(0 votes)

Original source: https://en.wikipedia.org/wiki/Linear compressor. Read more

|

Retrieved from "https://handwiki.org/wiki/index.php?title=Physics:Linear_compressor&oldid=3838308"
*[v]: View this template
*[t]: Discuss this template
*[e]: Edit this template