American wire gauge

North American standard for electrical wire diameters

"AWG" redirects here. For other uses, see AWG (disambiguation).

American Wire Gauge (AWG) is a logarithmic stepped standardized wire gauge system used since 1857, predominantly in North America, for the diameters of round, solid, nonferrous, electrically conducting wire. Dimensions of the wires are given in ASTM standard B 258.[1] The cross-sectional area of each gauge is an important factor for determining its current-carrying capacity.

## Origin

[edit]

The AWG originated in the number of drawing operations used to produce a given gauge of wire. Very fine wire (for example, 30 gauge) required more passes through the drawing dies than 0 gauge wire did. Manufacturers of wire formerly had proprietary wire gauge systems; the development of standardized wire gauges rationalized selection of wire for a particular purpose.

While the AWG is essentially identical to the Brown & Sharpe (B&S) sheet metal gauge, the B&S gauge was designed for use with sheet metals as its name suggests. These are functionally interchangeable but the use of B&S in relation to wire gauges, rather than sheet metal gauges, is technically improper.

## Specifications

[edit]

Increasing gauge numbers denote logarithmically decreasing wire diameters, which is similar to many other non-metric gauging systems such as British Standard Wire Gauge (SWG). However, AWG is dissimilar to IEC 60228, the metric wire-size standard used in most parts of the world, based directly on the wire cross-section area (in square millimetres, mm2).

The AWG tables are for a single, solid and round conductor. The AWG of a stranded wire is determined by the cross-sectional area of the equivalent solid conductor. Because there are also small gaps between the strands, a stranded wire will always have a slightly larger overall diameter than a solid wire with the same AWG.

### Formulae

[edit]

By definition, 36 AWG is 0.005 inches in diameter, and 0000 AWG is 0.46 inches in diameter. The ratio of these diameters is 1:92, and there are 40 gauge sizes from 36 to 0000, or 39 steps. Because each successive gauge number increases cross sectional area by a constant multiple, diameters vary geometrically. Any two successive gauges (e.g., A and B) have diameters whose ratio (dia. B ÷ dia. A) is  92 39 {\displaystyle {\sqrt[{39}]{92}}} (approximately 1.12293), while for gauges two steps apart (e.g., A, B, and C), the ratio of the C to A is about 1.122932 ≈ 1.26098. Similarly for gauges n steps apart the ratio of the first to last gauges is about 1.12293n.

The diameter of an AWG wire is determined according to the following formula:

d n = 0.005 i n c h × 92 ( 36 − n ) / 39 = 0.127 m m × 92 ( 36 − n ) / 39 {\displaystyle d_{n}=0.005~\mathrm {inch} \times 92^{(36-n)/39}=0.127~\mathrm {mm} \times 92^{(36-n)/39}}

(where n is the AWG size for gauges from 36 to 0, n = −1 for 00, n = −2 for 000, and n = −3 for 0000. See below for rule.)

or equivalently:

d n = e − 1.12436 − 0.11594 n i n c h = e 2.1104 − 0.11594 n m m {\displaystyle d_{n}=e^{-1.12436-0.11594n}\ \mathrm {inch} =e^{2.1104-0.11594n}\ \mathrm {mm} }

The gauge can be calculated from the diameter using [2]

n = − 39 log 92 ⁡ ( d n 0.005 i n c h ) + 36 = − 39 log 92 ⁡ ( d n 0.127 m m ) + 36 {\displaystyle n=-39\log _{92}\left({\frac {d_{n}}{0.005~\mathrm {inch} }}\right)+36=-39\log _{92}\left({\frac {d_{n}}{0.127~\mathrm {mm} }}\right)+36}

and the cross-section area is

A n = π 4 d n 2 ≈ 0.000019635 i n c h 2 × 92 ( 36 − n ) / 19.5 ≈ 0.012668 m m 2 × 92 ( 36 − n ) / 19.5 {\displaystyle A_{n}={\frac {\pi }{4}}d_{n}^{2}\approx 0.000019635~\mathrm {inch} ^{2}\times 92^{(36-n)/19.5}\approx 0.012668~\mathrm {mm} ^{2}\times 92^{(36-n)/19.5}} .

The standard ASTM B258-02 (2008), Standard Specification for Standard Nominal Diameters and Cross-Sectional Areas of AWG Sizes of Solid Round Wires Used as Electrical Conductors, defines the ratio between successive sizes to be the 39th root of 92, or approximately 1.1229322.[3] ASTM B258-02 also dictates that wire diameters should be tabulated with no more than 4 significant figures, with a resolution of no more than 0.0001 inches (0.1 mils) for wires thicker than 44 AWG, and 0.00001 inches (0.01 mils) for wires 45 AWG and thinner.

Sizes with multiple zeros are successively thicker than 0 AWG and can be denoted using "number of zeros/0", for example 4/0 AWG for 0000 AWG. For an m/0 AWG wire, use n = −(m − 1) = 1 − m in the above formulas. For instance, for 0000 AWG or 4/0 AWG, use n = −3.

#### Rules of thumb

[edit]

The sixth power of 39√92 is very close to 2,[4] which leads to the following rules of thumb:

* When the cross-sectional area of a wire is doubled, the AWG will decrease by 3. (E.g. two 14 AWG wires have about the same cross-sectional area as a single 11 AWG wire.) This doubles the conductance.
* When the diameter of a solid round wire is doubled, the AWG will decrease by 6. (E.g. 1 mm diameter wire is ~18 AWG, 2 mm diameter wire is ~12 AWG, and 4 mm diameter wire is ~6 AWG). This quadruples the cross-sectional area and conductance.
* A decrease of ten gauge numbers (E.g. from 12 AWG to 2 AWG) multiplies the area and weight by approximately 10, and reduces the electrical resistance (and increases the conductance) by a factor of approximately 10.

Convenient coincidences result in the following rules of thumb for resistances:

* The resistance of copper wire is approximately ⁠1 ohms/1000 feet⁠ for 10 AWG, ⁠10 ohms/1000 feet⁠ for 20 AWG, ⁠100 ohms/1000 feet⁠ for 30 AWG, and so on.[5]: 27
* Because aluminum wire has a conductivity of approximately 61% of copper, an aluminum wire has nearly the same resistance as a copper wire that is two sizes smaller, which has 62.9% of the area.

## Tables of AWG wire sizes

[edit]

The table below shows various data including both the resistance of the various wire gauges and the allowable current (ampacity) based on a copper conductor with plastic insulation. The diameter information in the table applies to solid wires. Stranded wires are calculated by calculating the equivalent cross sectional copper area. Fusing current (melting wire) is estimated based on 25 °C (77 °F) ambient temperature. The table below assumes DC, or AC frequencies equal to or less than 60 Hz, and does not take skin effect into account. "Turns of wire per unit length" is the reciprocal of the conductor diameter; it is therefore an upper limit for wire wound in the form of a helix (see solenoid), based on uninsulated wire.

AWG  | Diameter  | Turns of wire,
without
insulation  | Area  | Copper wire

|
|
|
|

Length-specific
resistance[6] | Ampacity at temperature rating[a] | Fusing current[9][10]
60 °C  | 75 °C  | 90 °C  | Preece[11][12][13][14] | Onderdonk[15][14]
(in)  | (mm)  | (per in)  | (per cm)  | (kcmil)  | (mm2)  | (mΩ/m[b])  | (mΩ/ft[c])  | (A)  | ~10 s  | 1 s  | 32 ms
0000 (4/0) | 0.4600[d] | 11.684[d] | 2.17 | 0.856 | 212 | 107 | 0.1608 | 0.04901 | 195 | 230 | 260 | 3.2 kA | 33 kA | 182 kA
000 (3/0) | 0.4096 | 10.405 | 2.44 | 0.961 | 168 | 85.0 | 0.2028 | 0.06180 | 165 | 200 | 225 | 2.7 kA | 26 kA | 144 kA
00 (2/0) | 0.3648 | 9.266 | 2.74 | 1.08 | 133 | 67.4 | 0.2557 | 0.07793 | 145 | 175 | 195 | 2.3 kA | 21 kA | 115 kA
0 (1/0) | 0.3249 | 8.251 | 3.08 | 1.21 | 106 | 53.5 | 0.3224 | 0.09827 | 125 | 150 | 170 | 1.9 kA | 16 kA | 91 kA
1 | 0.2893 | 7.348 | 3.46 | 1.36 | 83.7 | 42.4 | 0.4066 | 0.1239 | 110 | 130 | 145 | 1.6 kA | 13 kA | 72 kA
2 | 0.2576 | 6.544 | 3.88 | 1.53 | 66.4 | 33.6 | 0.5127 | 0.1563 | 95 | 115 | 130 | 1.3 kA | 10.2 kA | 57 kA
3 | 0.2294 | 5.827 | 4.36 | 1.72 | 52.6 | 26.7 | 0.6465 | 0.1970 | 85 | 100 | 115 | 1.1 kA | 8.1 kA | 45 kA
4 | 0.2043 | 5.189 | 4.89 | 1.93 | 41.7 | 21.2 | 0.8152 | 0.2485 | 70 | 85 | 95 | 946 A | 6.4 kA | 36 kA
5 | 0.1819 | 4.621 | 5.50 | 2.16 | 33.1 | 16.8 | 1.028 | 0.3133 |  | 795 A | 5.1 kA | 28 kA
6 | 0.1620 | 4.115 | 6.17 | 2.43 | 26.3 | 13.3 | 1.296 | 0.3951 | 55 | 65 | 75 | 668 A | 4.0 kA | 23 kA
7 | 0.1443 | 3.665 | 6.93 | 2.73 | 20.8 | 10.5 | 1.634 | 0.4982 |  | 561 A | 3.2 kA | 18 kA
8 | 0.1285 | 3.264 | 7.78 | 3.06 | 16.5 | 8.37 | 2.061 | 0.6282 | 40 | 50 | 55 | 472 A | 2.5 kA | 14 kA
9 | 0.1144 | 2.906 | 8.74 | 3.44 | 13.1 | 6.63 | 2.599 | 0.7921 |  | 396 A | 2.0 kA | 11 kA
10 | 0.1019 | 2.588 | 9.81 | 3.86 | 10.4 | 5.26 | 3.277 | 0.9989 | 30 | 35 | 40 | 333 A | 1.6 kA | 8.9 kA
11 | 0.0907 | 2.305 | 11.0 | 4.34 | 8.23 | 4.17 | 4.132 | 1.260 |  | 280 A | 1.3 kA | 7.1 kA
12 | 0.0808 | 2.053 | 12.4 | 4.87 | 6.53 | 3.31 | 5.211 | 1.588 | 20 | 25 | 30 | 235 A | 1.0 kA | 5.6 kA
13 | 0.0720 | 1.828 | 13.9 | 5.47 | 5.18 | 2.62 | 6.571 | 2.003 |  | 198 A | 798 A | 4.5 kA
14 | 0.0641 | 1.628 | 15.6 | 6.14 | 4.11 | 2.08 | 8.286 | 2.525 | 15 | 20 | 25 | 166 A | 633 A | 3.5 kA
15 | 0.0571 | 1.450 | 17.5 | 6.90 | 3.26 | 1.65 | 10.45 | 3.184 |  | 140 A | 502 A | 2.8 kA
16 | 0.0508 | 1.291 | 19.7 | 7.75 | 2.58 | 1.31 | 13.17 | 4.016 | 12 | 16 | 18 | 117 A | 398 A | 2.2 kA
17 | 0.0453 | 1.150 | 22.1 | 8.70 | 2.05 | 1.04 | 16.61 | 5.064 |  | 99 A | 316 A | 1.8 kA
18 | 0.0403 | 1.024 | 24.8 | 9.77 | 1.62 | 0.823 | 20.95 | 6.385 | 10 | 14 | 16 | 83 A | 250 A | 1.4 kA
19 | 0.0359 | 0.912 | 27.9 | 11.0 | 1.29 | 0.653 | 26.42 | 8.051 | — | — | — | 70 A | 198 A | 1.1 kA
20 | 0.0320 | 0.812 | 31.3 | 12.3 | 1.02 | 0.518 | 33.31 | 10.15 | 5 | 11 | — | 58.5 A | 158 A | 882 A
21 | 0.0285 | 0.723 | 35.1 | 13.8 | 0.810 | 0.410 | 42.00 | 12.80 | — | — | — | 49 A | 125 A | 700 A
22 | 0.0253 | 0.644 | 39.5 | 15.5 | 0.642 | 0.326 | 52.96 | 16.14 | 3 | 7 | — | 41 A | 99 A | 551 A
23 | 0.0226 | 0.573 | 44.3 | 17.4 | 0.509 | 0.258 | 66.79 | 20.36 | — | — | — | 35 A | 79 A | 440 A
24 | 0.0201 | 0.511 | 49.7 | 19.6 | 0.404 | 0.205 | 84.22 | 25.67 | 2.1 | 3.5 | — | 29 A | 62 A | 348 A
25 | 0.0179 | 0.455 | 55.9 | 22.0 | 0.320 | 0.162 | 106.2 | 32.37 | — | — | — | 24 A | 49 A | 276 A
26 | 0.0159 | 0.405 | 62.7 | 24.7 | 0.254 | 0.129 | 133.9 | 40.81 | 1.3 | 2.2 | — | 20 A | 39 A | 218 A
27 | 0.0142 | 0.361 | 70.4 | 27.7 | 0.202 | 0.102 | 168.9 | 51.47 | — | — | — | 17 A | 31 A | 174 A
28 | 0.0126 | 0.321 | 79.1 | 31.1 | 0.160 | 0.0810 | 212.9 | 64.90 | 0.83 | 1.4 | — | 14 A | 24 A | 137 A
29 | 0.0113 | 0.286 | 88.8 | 35.0 | 0.127 | 0.0642 | 268.5 | 81.84 | — | — | — | 12 A | 20 A | 110 A
30 | 0.0100 | 0.255 | 99.7 | 39.3 | 0.101 | 0.0509 | 338.6 | 103.2 | 0.52 | 0.86 | — | 10 A | 15 A | 86 A
31 | 0.00893 | 0.227 | 112 | 44.1 | 0.0797 | 0.0404 | 426.9 | 130.1 | — | — | — | 9 A | 12 A | 69 A
32 | 0.00795 | 0.202 | 126 | 49.5 | 0.0632 | 0.0320 | 538.3 | 164.1 | 0.32 | 0.53 | — | 7 A | 10 A | 54 A
33 | 0.00708 | 0.180 | 141 | 55.6 | 0.0501 | 0.0254 | 678.8 | 206.9 | — | — | — | 6 A | 7.7 A | 43 A
34 | 0.00630 | 0.160 | 159 | 62.4 | 0.0398 | 0.0201 | 856.0 | 260.9 | 0.18 | 0.3 | — | 5 A | 6.1 A | 34 A
35 | 0.00561 | 0.143 | 178 | 70.1 | 0.0315 | 0.0160 | 1079 | 329.0 | — | — | — | 4 A | 4.8 A | 27 A
36 | 0.00500[d] | 0.127[d] | 200 | 78.7 | 0.0250 | 0.0127 | 1361 | 414.8 | — | — | — | 4 A | 3.9 A | 22 A
37 | 0.00445 | 0.113 | 225 | 88.4 | 0.0198 | 0.0100 | 1716 | 523.1 | — | — | — | 3 A | 3.1 A | 17 A
38 | 0.00397 | 0.101 | 252 | 99.3 | 0.0157 | 0.00797 | 2164 | 659.6 | — | — | — | 3 A | 2.4 A | 14 A
39 | 0.00353 | 0.0897 | 283 | 111 | 0.0125 | 0.00632 | 2729 | 831.8 | — | — | — | 2 A | 1.9 A | 11 A
40 | 0.00314 | 0.0799 | 318 | 125 | 0.00989 | 0.00501 | 3441 | 1049 | — | — | — | 1 A | 1.5 A | 8.5 A

1. ^ For enclosed wire at 30 °C ambient,[7] with given insulation material temperature rating, or for single unbundled wires in equipment for 16 AWG and thinner.[8]
2. ^ or, equivalently, Ω/km
3. ^ or, equivalently, Ω/kft
4. ^ a b c d Exactly, by definition

In the North American electrical industry, conductors thicker than 4/0 AWG are generally identified by the area in thousands of circular mils (kcmil), where 1 kcmil = 0.5067 mm2. The next wire size thicker than 4/0 has a cross section of 250 kcmil. A circular mil is the area of a wire one mil in diameter. One million circular mils is the area of a circle with 1,000 mil (1 inch) diameter. An older abbreviation for one thousand circular mils is MCM.

## Stranded wire AWG sizes

[edit]

AWG can also be used to describe stranded wire. The AWG of a stranded wire represents the sum of the cross-sectional diameter of the individual strands; the gaps between strands are not counted. When made with circular strands, these gaps occupy about 25% of the wire area, thus requiring the overall bundle diameter to be about 13% larger than a solid wire of equal gauge.

Stranded wires are specified with three numbers, the overall AWG size, the number of strands, and the AWG size of a strand. The number of strands and the AWG of a strand are separated by a slash. For example, a 22 AWG 7/30 stranded wire is a 22 AWG wire made from seven strands of 30 AWG wire.

As indicated in the Formulas and Rules of Thumb sections above, differences in AWG translate directly into ratios of diameter or area. This property can be employed to easily find the AWG of a stranded bundle by measuring the diameter and count of its strands. (This only applies to bundles with circular strands of identical size.) To find the AWG of 7-strand wire with equal strands, subtract 8.4 from the AWG of a strand. Similarly, for 19-strand subtract 12.7, and for 37 subtract 15.6.

Measuring strand diameter is often easier and more accurate than attempting to measure bundle diameter and packing ratio. Such measurement can be done with a wire gauge go-no-go tool or with a caliper or micrometer.

## Nomenclature and abbreviations in electrical distribution

[edit]

Main article: Electric power distribution

Alternative ways are commonly used in the electrical industry to specify wire sizes as AWG.

* 4 AWG (proper)
* #4 (the number sign is used as an abbreviation of "number")
* № 4 (the numero sign is used as an abbreviation for "number")
* No. 4 (an approximation of the numero is used as an abbreviation for "number")
* No. 4 AWG
* 4 ga. (abbreviation for "gauge")
* 000 AWG (proper for thick sizes)
* 3/0 (common for thick sizes) Pronounced "three-aught"
* 3/0 AWG
* #000

### Pronunciation

[edit]

AWG is colloquially referred to as gauge and the zeros in thick wire sizes are referred to as aught /ˈɔːt/. Wire sized 1 AWG is referred to as "one gauge" or "No. 1" wire; similarly, thinner sizes are pronounced "x gauge" or "No. x" wire, where x is the positive-integer AWG number. Consecutive AWG wire sizes thicker than No. 1 wire are designated by the number of zeros:

* No. 0, often written 1/0 and referred to as "one aught" wire
* No. 00, often written 2/0 and referred to as "two aught" wire
* No. 000, often written 3/0 and referred to as "three aught" wire

and so on.

## See also

[edit]

* IEC 60228, international standards for wire sizes
* French gauge
* Brown & Sharpe
* Circular mil, North American Electrical industry standard for wires thicker than 4/0.
* Birmingham Wire Gauge
* Stubs Iron Wire Gauge
* Jewelry wire gauge
* Body jewelry sizes, which commonly uses AWG (especially for thinner sizes), even when the material is not metallic.[16]
* Electrical wiring
* Number 8 wire, a term used in the New Zealand vernacular

## References

[edit]

1. ^ "ASTM B258-14 Standard Specification for Standard Nominal Diameters and Cross-sectional Areas of AWG Sizes of Solid Round Wires Used as Electrical Conductors". West Conshohocken: ASTM International. Archived from the original on 22 July 2014. Retrieved 22 March 2015.
2. ^ The logarithm to the base 92 can be computed using any other logarithm, such as common or natural logarithm, using log92x = (log x)/(log 92).
3. ^ ASTM Standard B258-02, page 4
4. ^ The result is roughly 2.0050, or one-quarter of one percent higher than 2
5. ^ Copper Wire Tables (Technical report). Circular of the Bureau of Standards No. 31 (3rd ed.). United States Department of Commerce. October 1, 1914.
6. ^ Figure for solid copper wire at 68 °F, (Not in accordance to NEC Codebook 2014 Ch. 9, Table 8) computed based on 100% IACS conductivity of 58.0 MS/m, which agrees with multiple sources:
* Lund, Mark. "American Wire Gauge table and AWG Electrical Current Load Limits". Powerstream.com. Retrieved 2008-05-02. (although the ft/m conversion seems slightly erroneous)
* Belden Master Catalog, 2006, although data from there for gauges 35 and 37–40 seems obviously wrong.
High-purity oxygen-free copper can achieve up to 101.5% IACS conductivity; e.g., the Kanthal conductive alloys data sheet lists slightly lower resistances than this table.
7. ^ NFPA 70 National Electrical Code 2014 Edition Archived 2008-10-15 at the Wayback Machine. Table 310.15(B)(16) (formerly Table 310.16) page 70-161, "Allowable ampacities of insulated conductors rated 0 through 2000 volts, 60°C through 90°C, not more than three current-carrying conductors in raceway, cable, or earth (directly buried) based on ambient temperature of 30°C." Extracts from NFPA 70 do not represent the full position of NFPA and the original complete Code must be consulted. In particular, the maximum permissible overcurrent protection devices may set a lower limit.
8. ^ "Table 11: Recommended Current Ratings (Continuous Duty) for electronic equipment and chassis wiring". Reference Data for Engineers: Radio, Electronics, Computer and Communications (7th ed.). pp. 49–16.
9. ^ Computed using equations from Beaty, H. Wayne; Fink, Donald G., eds. (2007), The Standard Handbook for Electrical Engineers (15th ed.), McGraw Hill, pp. 4–25, ISBN 978-0-07-144146-9
10. ^ Brooks, Douglas G. (December 1998), "Fusing Current: When Traces Melt Without a Trace" (PDF), Printed Circuit Design, 15 (12): 53, archived from the original (PDF) on 2016-03-27, retrieved 2016-08-01
11. ^ Preece, W. H. (1883), "On the Heating Effects of Electric Currents", Proceedings of the Royal Society (36): 464–471
12. ^ Preece, W. H. (1887), "On the Heating Effects of Electric Currents", Proceedings of the Royal Society, II (43): 280–295
13. ^ Preece, W. H. (1888), "On the Heating Effects of Electric Currents", Proceedings of the Royal Society, III (44): 109–111
14. ^ a b Brooks, Douglas G.; Adam, Johannes (29 June 2015), "Who Were Preece and Onderdonk?", Printed Circuit Design and Fab
15. ^ Stauffacher, E. R. (June 1928), "Short-time Current Carrying Capacity of Copper Wire" (PDF), General Electric Review, 31 (6)
16. ^ SteelNavel.com Body Piercing Jewelry Size Reference — illustrating the different ways that size is measured on different kinds of jewelry

* v
* t
* e

United States customary units

Comparison with imperial unit system

Length|

* Thousandth of an inch
* Inch
* Hand
* Link
* Foot
* Yard
* Rod
* Chain
* Furlong
* Mile
* statute

Area|

* Square inch
* Square foot
* Square yard
* Acre
* Square mile

Volume|

| Derived|

* Cubic inch
* Cubic foot
* Cubic yard
* Cubic mile

|

Cooking|

* Teaspoon
* Tablespoon
* Fluid ounce
* Cup
* Pint
* Quart
* Gallon

Wood|

* Board foot
* Cord
* Face cord

Other|

* Minim
* Gill
* Peck
* Bushel
* Barrel
* Acre-foot

Speed|

* Feet per second
* Miles per hour

Mass|

* Grain
* Dram
* Ounce
* Pound
* Hundredweight
* Ton
* Long
* Short

Force|

* Poundal
* Pound-force
* Kip

Pressure|

* Inch of mercury
* Pounds per square inch
* Kilopounds per square inch

Other units and measures|

* Bolt (cloth)
* British thermal unit
* Degree (angle)
* Fahrenheit
* Foot-candle
* Foot-lambert
* Foot-pound (energy)
* Horsepower
* Perm
* Pound-foot (torque)
* Spinning count
* Ton of refrigeration

Related systems|

* American wire gauge
* Avoirdupois system
* Body jewelry sizes
* English Engineering Units
* Foot–pound–second system of units

*[v]: View this template
*[t]: Discuss this template
*[e]: Edit this template