Condenser (heat transfer)

System for condensing gas into liquid by cooling

For condensers not involving heat transfer, see Condenser (disambiguation).

This article needs additional citations for verification. Please help improve this article by adding citations to reliable sources. Unsourced material may be challenged and removed.
Find sources: "Condenser" heat transfer – news · newspapers · books · scholar · JSTOR (March 2015) (Learn how and when to remove this message)

|

The condenser coil of a refrigerator

In systems involving heat transfer, a condenser is a heat exchanger used to condense a gaseous substance into a liquid state through cooling. In doing so, the latent heat is released by the substance and transferred to the surrounding environment. Condensers are used for efficient heat rejection in many industrial systems. Condensers can be made according to numerous designs and come in many sizes ranging from rather small (hand-held) to very large (industrial-scale units used in plant processes). For example, a refrigerator uses a condenser to get rid of heat extracted from the interior of the unit to the outside air.

Condensers are used in air conditioning, industrial chemical processes such as distillation, steam power plants, and other heat-exchange systems. The use of cooling water or surrounding air as the coolant is common in many condensers.[1]

## History

[edit]

This section needs expansion. You can help by adding to it. (September 2019)

|

The earliest laboratory condenser, a "Gegenstromkühler" (counter-flow condenser), was invented in 1771 by the Swedish-German chemist Christian Weigel.[2] By the mid-19th century, German chemist Justus von Liebig would provide his own improvements on the preceding designs of Weigel and Johann Friedrich August Göttling, with the device becoming known as the Liebig condenser.[3]

## Principle of operation

[edit]

A condenser is designed to transfer heat from a working fluid (e.g. water in a steam power plant) to a secondary fluid or the surrounding air. The condenser relies on the efficient heat transfer that occurs during phase changes, in this case during the condensation of a vapor into a liquid. The vapor typically enters the condenser at a temperature above that of the secondary fluid. As the vapor cools, it reaches the saturation temperature, condenses into liquid, and releases large quantities of latent heat. As this process occurs along the condenser, the quantity of vapor decreases and the quantity of liquid increases; at the outlet of the condenser, only liquid remains. Some condenser designs contain an additional length to subcool this condensed liquid below the saturation temperature.[4]

Countless variations exist in condenser design, with design variables including the working fluid, the secondary fluid, the geometry, and the material. Common secondary fluids include water, air, refrigerants, or phase-change materials.

Condensers have two significant design advantages over other cooling technologies:

* Heat transfer by latent heat is much more efficient than heat transfer by sensible heat only
* The temperature of the working fluid stays relatively constant during condensation, which maximizes the temperature difference between the working and secondary fluid.

## Examples of condensers

[edit]

### Surface condenser

[edit]

A surface condenser is one in which condensing medium and vapors are physically separated and used when direct contact is not desired. It is a shell and tube heat exchanger installed at the outlet of every steam turbine in thermal power stations. Commonly, the cooling water flows through the tube side and the steam enters the shell side where the condensation occurs on the outside of the heat transfer tubes. The condensate drips down and collects at the bottom, often in a built-in pan called a hotwell. The shell side often operates at a vacuum or partial vacuum, produced by the difference in specific volume between the steam and condensate. Conversely, the vapor can be fed through the tubes with the coolant water or air flowing around the outside.

### Chemistry

[edit]

Main article: Condenser (laboratory)

In chemistry, a condenser is the apparatus that cools hot vapors, causing them to condense into a liquid. Examples include the Liebig condenser, Graham condenser, and Allihn condenser. This is not to be confused with a condensation reaction which links two fragments into a single molecule by an addition reaction and an elimination reaction.

In laboratory distillation, reflux, and rotary evaporators, several types of condensers are commonly used. The Liebig condenser is simply a straight tube within a cooling water jacket and is the simplest (and relatively least expensive) form of condenser. The Graham condenser is a spiral tube within a water jacket, and the Allihn condenser has a series of large and small constrictions on the inside tube, each increasing the surface area upon which the vapor constituents may condense. Being more complex shapes to manufacture, these latter types are also more expensive to purchase. These three types of condensers are laboratory glassware items since they are typically made of glass. Commercially available condensers usually are fitted with ground glass joints and come in standard lengths of 100, 200, and 400 mm. Air-cooled condensers are unjacketed, while water-cooled condensers contain a jacket for the water.

### Industrial distillation

[edit]

Larger condensers are also used in industrial-scale distillation processes to cool distilled vapor into liquid distillate. Commonly, the coolant flows through the tube side and distilled vapor through the shell side with distillate collecting at or flowing out the bottom.

### Air conditioning

[edit]

Condenser unit for central air conditioning for a typical house Rooftop condenser unit fitted on top of an Osaka Municipal Subway 10 series subway carriage (April 2008)

A condenser unit used in central air conditioning systems typically has a heat exchanger section to cool down and condense incoming refrigerant vapor into liquid, a compressor to raise the pressure of the refrigerant and move it along, and a fan for blowing outside air through the heat exchanger section to cool the refrigerant inside. A typical configuration of such a condenser unit is as follows: The heat exchanger section wraps around the sides of the unit with the compressor inside. In this heat exchanger section, the refrigerant goes through multiple tube passes, which are surrounded by heat transfer fins through which cooling air can circulate from outside to inside the unit. This also increases the surface area. There is a motorized fan inside the condenser unit near the top, which is covered by some grating to keep any objects from accidentally falling inside on the fan. The fan is used to pull outside cooling air in through the heat exchanger section at the sides and blow it out the top through the grating. These condenser units are located on the outside of the building they are trying to cool, with tubing between the unit and building, one for vapor refrigerant entering and another for liquid refrigerant leaving the unit. Of course, an electric power supply is needed for the compressor and fan inside the unit.

### Direct-contact

[edit]

In a direct-contact condenser, hot vapor and cool liquid are introduced into a vessel and allowed to mix directly, rather than being separated by a barrier such as the wall of a heat exchanger tube. The vapor gives up its latent heat and condenses to a liquid, while the liquid absorbs this heat and undergoes a temperature rise. The entering vapor and liquid typically contain a single condensable substance, such as a water spray being used to cool air and adjust its humidity.

## Equation

[edit]

For an ideal single-pass condenser whose coolant has constant density, constant heat capacity, linear enthalpy over the temperature range, perfect cross-sectional heat transfer, and zero longitudinal heat transfer, and whose tubing has constant perimeter, constant thickness, and constant heat conductivity, and whose condensible fluid is perfectly mixed and at a constant temperature, the coolant temperature varies along its tube according to:

Θ ( x ) = T H − T ( x ) T H − T ( 0 ) = e − N T U = e − h P x m ˙ c = e − G x m ˙ c L {\displaystyle \Theta (x)={\frac {T_{H}-T(x)}{T_{H}-T(0)}}=e^{-NTU}=e^{-{\frac {hPx}{{\dot {m}}c}}}=e^{-{\frac {Gx}{{\dot {m}}cL}}}}

where:

* x {\displaystyle x} is the distance from the coolant inlet
* T ( x ) {\displaystyle T(x)} is the coolant temperature, and T(0) the coolant temperature at its inlet
* T H {\displaystyle T_{H}} is the hot fluid's temperature
* N T U {\displaystyle NTU} is the number of transfer units
* m {\displaystyle m} is the coolant's mass (or other) flow rate
* c {\displaystyle c} is the coolant's heat capacity at constant pressure per unit mass (or other)
* h {\displaystyle h} is the heat transfer coefficient of the coolant tube
* P {\displaystyle P} is the perimeter of the coolant tube
* G {\displaystyle G} is the heat conductance of the coolant tube (often denoted  U A {\displaystyle UA} )
* L {\displaystyle L} is the length of the coolant tube

## See also

[edit]

* Condenser (laboratory)
* Air well (condenser)

## References

[edit]

Wikimedia Commons has media related to Condensers.

1. ^ Hindelang, Man jjhat; Palazzolo, Joseph; Robertson, Matthew, "Condensers", Encyclopedia of Chemical Engineering Equipment, University of Michigan, archived from the original on 24 December 2012
2. ^ Weigel, Christian Ehrenfried (1771). Christian Ehrenfried Weigel, Volume 1 (in Latin). Goettingae (Göttingen): Aere Dieterichiano. pp. 8–11. Retrieved 16 September 2019.
3. ^ Liebig, Justus von; Poggendorff, J.C.; Wöhler, Fr. (eds.) (1842), Handwörterbuch der reinen und angewandten Chemie [Dictionary of pure and applied chemistry], vol. 2 (in German). Braunschweig, Germany: Friedrich Vieweg und Sohn. Article: "Destillation," pp. 526–554.
4. ^ Kays, W.M.; London, A.L. (January 1984), "Condensers", Compact Heat Exchangers, OSTI, OSTI 6132549

* v
* t
* e

Heating, ventilation, and air conditioning

Fundamental
concepts|

* Air changes per hour (ACH)
* Bake-out
* Building envelope
* Convection
* Dilution
* Domestic energy consumption
* Enthalpy
* Fluid dynamics
* Gas compressor
* Heat pump and refrigeration cycle
* Heat transfer
* Humidity
* Infiltration
* Latent heat
* Noise control
* Outgassing
* Particulates
* Psychrometrics
* Sensible heat
* Stack effect
* Thermal comfort
* Thermal destratification
* Thermal mass
* Thermodynamics
* Vapour pressure of water

Technology|

* Absorption-compression heat pump
* Absorption refrigerator
* Air barrier
* Air conditioning
* Antifreeze
* Automobile air conditioning
* Autonomous building
* Building insulation materials
* Central heating
* Central solar heating
* Chilled beam
* Chilled water
* Constant air volume (CAV)
* Coolant
* Cross ventilation
* Dedicated outdoor air system (DOAS)
* Deep water source cooling
* Demand controlled ventilation (DCV)
* Displacement ventilation
* District cooling
* District heating
* Electric heating
* Energy recovery ventilation (ERV)
* Firestop
* Forced-air
* Forced-air gas
* Free cooling
* Heat recovery ventilation (HRV)
* Hybrid heat
* Hydronics
* Ice storage air conditioning
* Kitchen ventilation
* Mixed-mode ventilation
* Microgeneration
* Passive cooling
* Passive daytime radiative cooling
* Passive house
* Passive ventilation
* Radiant heating and cooling
* Radiant cooling
* Radiant heating
* Radon mitigation
* Refrigeration
* Renewable heat
* Room air distribution
* Solar air heat
* Solar combisystem
* Solar cooling
* Solar heating
* Thermal insulation
* Thermosiphon
* Underfloor air distribution
* Underfloor heating
* Vapor barrier
* Vapor-compression refrigeration (VCRS)
* Variable air volume (VAV)
* Variable refrigerant flow (VRF)
* Ventilation
* Water heat recycling

Components|

* Air conditioner inverter
* Air door
* Air filter
* Air handler
* Air ionizer
* Air-mixing plenum
* Air purifier
* Air source heat pump
* Attic fan
* Automatic balancing valve
* Back boiler
* Barrier pipe
* Blast damper
* Boiler
* Centrifugal fan
* Ceramic heater
* Chiller
* Condensate pump
* Condenser
* Condensing boiler
* Convection heater
* Compressor
* Cooling tower
* Damper
* Dehumidifier
* Duct
* Economizer
* Electrostatic precipitator
* Evaporative cooler
* Evaporator
* Exhaust hood
* Expansion tank
* Fan
* Fan coil unit
* Fan filter unit
* Fan heater
* Fire damper
* Fireplace
* Fireplace insert
* Freeze stat
* Flue
* Freon
* Fume hood
* Furnace
* Gas compressor
* Gas heater
* Gasoline heater
* Grease duct
* Grille
* Ground-coupled heat exchanger
* Ground source heat pump
* Heat exchanger
* Heat pipe
* Heat pump
* Heating film
* Heating system
* HEPA
* High efficiency glandless circulating pump
* High-pressure cut-off switch
* Humidifier
* Infrared heater
* Inverter compressor
* Kerosene heater
* Louver
* Mechanical room
* Oil heater
* Packaged terminal air conditioner
* Plenum space
* Pressurisation ductwork
* Process duct work
* Radiator
* Radiator reflector
* Recuperator
* Refrigerant
* Register
* Reversing valve
* Run-around coil
* Sail switch
* Scroll compressor
* Solar chimney
* Solar-assisted heat pump
* Space heater
* Smoke canopy
* Smoke damper
* Smoke exhaust ductwork
* Thermal expansion valve
* Thermal wheel
* Thermostatic radiator valve
* Trickle vent
* Trombe wall
* TurboSwing
* Turning vanes
* Ultra-low particulate air (ULPA)
* Whole-house fan
* Windcatcher
* Wood-burning stove
* Zone valve

Measurement
and control|

* Air flow meter
* Aquastat
* BACnet
* Blower door
* Building automation
* Carbon dioxide sensor
* Clean air delivery rate (CADR)
* Control valve
* Gas detector
* Home energy monitor
* Humidistat
* HVAC control system
* Infrared thermometer
* Intelligent buildings
* LonWorks
* Minimum efficiency reporting value (MERV)
* Normal temperature and pressure (NTP)
* OpenTherm
* Programmable communicating thermostat
* Programmable thermostat
* Psychrometrics
* Room temperature
* Smart thermostat
* Standard temperature and pressure (STP)
* Thermographic camera
* Thermostat
* Thermostatic radiator valve

Professions,
trades,
and services|

* Architectural acoustics
* Architectural engineering
* Architectural technologist
* Building services engineering
* Building information modeling (BIM)
* Deep energy retrofit
* Duct cleaning
* Duct leakage testing
* Environmental engineering
* Hydronic balancing
* Kitchen exhaust cleaning
* Mechanical engineering
* Mechanical, electrical, and plumbing
* Mold growth, assessment, and remediation
* Refrigerant reclamation
* Testing, adjusting, balancing

Industry
organizations|

* AHRI
* AMCA
* ASHRAE
* ASTM International
* BRE
* BSRIA
* CIBSE
* Institute of Refrigeration
* IIR
* LEED
* SMACNA
* UMC

Health and safety|

* Indoor air quality (IAQ)
* Passive smoking
* Sick building syndrome (SBS)
* Volatile organic compound (VOC)

See also|

* ASHRAE Handbook
* Building science
* Fireproofing
* Glossary of HVAC terms
* Warm Spaces
* World Refrigeration Day
* Template:Fire protection
* Template:Home automation
* Template:Solar energy

* v
* t
* e

Steam engines

Operating cycle|

* Atmospheric
* Watt
* Cornish
* Compound
* Uniflow

Valves|

| Valves|

* Slide
* D slide
* Piston
* Drop
* Corliss
* Poppet
* Sleeve
* Bash

|

Valve gear|

* Gab
* Stephenson link
* Joy
* Walschaerts
* Allan
* Baker
* Corliss
* Lentz
* Caprotti
* Gresley conjugated
* Southern

Mechanisms|

* Beam
* Cataract
* Centrifugal governor
* Connecting rod
* Crank
* Crankshaft
* Tusi couple hypocycloidal straight line mechanism
* Link chain
* Parallel motion
* Plate chain
* Rotative beam
* Sun and planet gear
* Watt's linkage

Boilers|

| Simple boilers|

* Haystack
* Wagon
* Egg-ended
* Box
* Flued
* Cornish
* Lancashire

|

Fire-tube boilers|

* Locomotive
* Scotch
* Launch

Water-tube boilers|

* Babcock & Wilcox
* Field-tube
* Sentinel
* Stirling
* Thimble tube
* Three-drum
* Yarrow

Boiler feed|

* Feedwater heater
* Feedwater pump
* Injector

Cylinder|

* Locomotive
* Oscillating
* Single- and double-acting

Condenser|

* Condensing steam locomotive
* Jet
* Kirchweger
* Watt's separate
* "Pickle-pot"
* Surface

Other|

* Blowback
* Crosshead
* Cutoff
* Expansion valve
* Hydrolock
* Piston
* Reciprocating engine
* Return connecting rod engine
* Six-column beam engine
* Steeple engine
* Safety valve
* Steeple compound engine
* Stroke
* Working fluid

History|

| Precursors|

* Savery Engine (1698)

|

Newcomen engine|

* Newcomen Memorial Engine (1725)
* Fairbottom Bobs (1760)
* Elsecar Engine (1795)

Watt engine|

| Beam|

* Kinneil Engine (1768)
* Old Bess (1777)
* Chacewater Mine engine (1778)
* Smethwick Engine (1779)
* Resolution (1781)

|

Rotative beam|

* Soho Manufactory engine (1782)
* Bradley Works engine (1783)
* Whitbread Engine (1785)
* National Museum of Scotland engine (1786)
* Lap Engine (1788)

High-pressure|

* Richard Trevithick
* Puffing Devil (1801)
* London Steam Carriage (1803)
* "Coalbrookdale Locomotive" (1803)
* "Pen-y-Darren" locomotive (1804)

Compound|

* Woolf's compound engine (1803)

Murray|

* Murray's Hypocycloidal Engine (1805)
* Salamanca (1812)

High-speed|

* Porter-Allen (1862)
* Ljungström (1908)

See also|

* Glossary of steam locomotive components
* History of steam road vehicles
* Cugnot's fardier à vapeur (1769)
* Murdoch's model steam carriage (1784)
* Lean's Engine Reporter
* List of steam technology patents
* Modern steam
* Stationary steam engine
* Timeline of steam power
* Water-returning engine

Authority control databases: National |

* Japan

|

*[v]: View this template
*[t]: Discuss this template
*[e]: Edit this template