Fukushima nuclear accident (Unit 2 Reactor)

One of the reactors involved in the Fukushima nuclear accident

Fukushima Daiichi (Unit 2 Reactor)

Overhead view of the complex, Unit 2 is the second one from the right (blue cladding still largely in place).

General information
Status| Severely damaged
Type| Reactor
Location| Ōkuma and Futaba, Fukushima, Japan
Coordinates| 37°25′17″N 141°1′57″E﻿ / ﻿37.42139°N 141.03250°E﻿ / 37.42139; 141.03250
Construction started| 9 June 1969[1]
Completed| 10 October 1970[1]
Opened| 18 July 1974[1]
Closed| 19 May 2011
(shutdown)[1]
External videos

24 hours live camera for Fukushima Daiichi nuclear disaster on YouTube, certified by Tokyo Electric Power Co. Inc.

The Fukushima Daiichi (Unit 2) reactor, was 1 out of 4 reactors seriously affected during the Fukushima Daiichi nuclear disaster (福島第一原子力発電所事故, Fukushima Dai-ichi) on 11 March 2011.[2][3] Overall, the plant had 6 separate boiling water reactors originally designed by General Electric (GE), and maintained by the Tokyo Electric Power Company (TEPCO). At the time of the earthquake, Reactor 4 had been de-fueled while 5 and 6 were in cold shutdown for planned maintenance.[4]

## Background

[edit]

The plant comprises six separate boiling water reactors originally designed by General Electric (GE), and maintained by the Tokyo Electric Power Company (TEPCO). At the time of the quake, Unit 4 had been de-fueled while 5 and 6 were in cold shutdown for planned maintenance.[4] Unit 2 was operating at the time of the earthquake and experienced the same controlled initial shutdown as the other units.[5] As with unit 1, the reactor scrammed following the earthquake. The two diesel generators came online and initially all cooling systems were available. Initially the high pressure coolant injection (HPCI) system was primary cooling the core and at 15:00 operators activated the residual heat removal system main pump and the containment vessel spray pump at 15:07 to cool the suppression pool; all these systems failed following both AC power and DC power loss after the tsunami as the diesel generators and other systems failed when the tsunami overran the plant. The reactor core isolation cooling (RCIC) system was manually activated by operators at 15:39 following power loss, but by midnight the status of the reactor was unclear; some monitoring equipment was still operating on temporary power.[6] The coolant level was stable and preparations were underway to reduce pressure in the reactor containment vessel should it become necessary, though TEPCO did not state in press releases what these preparations were, and the government had been advised that this might happen.[7]

## Disaster

[edit]

Failure of both Unit 2 diesel generators

### Cooling problems

[edit]

TEPCO reported that the RCIC shut down around 19:00 JST on 12 March, and that the reactor containment vessel started reducing pressure before midnight.[8] The IAEA later revealed that no venting had taken place at the plant.[9] The following day at 09:00 JST, the RCIC was reported to be operating again.[10] A New York Times report suggested that plant officials initially concentrated efforts on a damaged fuel storage pool at Unit 2, diverting attention from problems arising at the other reactors, but that incident was not reported in official press releases.[11] The IAEA reported that on 14 March at 09:30, the RCIC was still operating and that power was being provided by a mobile generator.[9] At some point during the day TEPCO reported the shutdown of the RCIC system presumably due to low reactor pressure. Operators had for days taken measures to prevent the reactor pressure from dropping below the level at which the RCIC can operate to keep it running as long as possible. The system though, was never designed to be used for an extended period.[12] Fuel rods had been fully exposed for 140 minutes and there was a risk of a core meltdown.[13] Reactor water level indicators were reported to be showing minimum-possible values at 19:30 JST on 14 March.[14] Meanwhile, radiation dose rates measured at the gate of the plant (at 21:37 JST) reached a maximum of 3.13 m Sv/h, which was enough to reach the annual limit for non-nuclear workers in twenty minutes.[13] These levels later subsided as another measurement taken at 22:35 showed a lower reading of 0.326 mSv/h.[15] Workers concurrently succeeded in refilling half the reactor with water but parts of the rods were still exposed, and technicians could not rule out the possibility that some had melted. It was believed that around 23:00 JST, the 4 m long fuel rods in the reactor were fully exposed for the second time.[13][16]

At 00:30 JST on 15 March, NHK ran a live press conference with TEPCO stating that the water level had sunk under the rods once again and pressure in the vessel was raised. The utility said that the hydrogen explosion at Unit 3 might have caused a glitch in the cooling system of Unit 2: Four out of five water pumps being used to cool the Unit 2 reactor had failed after the explosion at Unit 3. In addition, the last pump had briefly stopped working when its fuel ran out.[17][18] To replenish the water, the contained pressure would have to be lowered first by opening a valve of the vessel. The unit's air flow gauge was accidentally turned off and, with the gauge turned off, flow of water into the reactor was blocked leading to full exposure of the rods. Water was later pumped into Unit 2 again by 04:11 JST.[19] It was later revealed that workers were minutes from restoring power to the standby liquid control (SLC) system pumps in unit 2 as a way to inject borated water once the RCIC shut down and had spent hours laying cable from a generator truck to the unit 2 power center when the unit 1 explosion occurred. This damaged the cable preventing this method from being used. It is possible this system could have prevented a complete meltdown as it took hours after the explosion until injection using fire trucks could be started.[20]

### Hydrogen explosion

[edit]

Radiation spike during the explosion of Unit 2

After Unit 3 exploded from built up hydrogen gas, the debris blew holes through the walls of Unit 2. It was initially hoped that these holes would vent any hydrogen gas coming from Unit 2 and prevent a similar explosion.[13] This unfortunately did not hold true as an explosion was heard after 06:14 JST on 15 March in Unit 2, possibly damaging the pressure-suppression system at the bottom part of the containment vessel.[21][22][23] The radiation level was reported as exceeding the legal limit, and the plant's operator started to evacuate all non-essential workers from the plant.[24] Only a minimum crew of 50 men, also referred to as the Fukushima 50, was left at the site.[25] Soon after, radiation equivalent dose rates had risen to 8.2 mSv/h[26] around two hours after the explosion and again down to 2.4 mSv/h, shortly after.[27] Three hours after the explosion, the rates had risen to 11.9 mSv/h.[28]

While admitting that the suppression pool at the bottom of the containment vessel had been damaged in the explosion, causing a drop of pressure there, Japanese nuclear authorities emphasized that the containment had not been breached as a result of the explosion and contained no obvious holes.[29] In a news conference on 15 March the director general of the IAEA, Yukiya Amano, said that there was a "possibility of core damage" at Unit 2 of less than 5%.[30] Japan's Nuclear and Industrial Safety Agency (NISA) stated 33% of the fuel rods were damaged, in news reports the morning of 16 March.[31] In the week that followed concerns were raised over a possible breach from the explosion at either the suppression pool, or the reactor vessel.[32][33] Images taken by a robotic inspection in 2012 later revealed superficial surface damage to pipework, but show the outer surface of the torus to be in normal condition. The potential break points of the manhole covers were also found to be intact.[34]

### Meltdown and seawater used for cooling

[edit]

Seawater-contamination along coast with caesium-137, from 21 March until 5 May (Source: GRS)

In their attempt to prevent a meltdown, the government ordered that seawater be used to cool the reactors as no alternatives were available at the time. At 20:05 JST on 14 March, the Japanese government ordered seawater to be injected into Unit 2 in a new effort to cool the reactor core. This process was later changed to fresh water and then back to sea water.[35] It was initially thought that Unit 2 had been spared a meltdown, but this notion soon came into question. On 29 March, Richard Lahey, former head of safety research for boiling-water reactors at General Electric, speculated that the reactor core may have melted through the reactor containment vessel onto a concrete floor, raising concerns of a major release of radioactive material, while failing to divulge the report by Dale G. Bridenbaugh which condemned the design as "unsafe".[36] On 27 April, TEPCO revised its estimate of damaged fuel in Unit 2 from 30% to 35%.[37] TEPCO finally confirmed on 23 May that Unit 2 suffered a meltdown about 100 hours after the earthquake.[38]

Tepco-workers were able to enter the building of reactor 2 a month later where they installed and replaced a provisional gauge for measuring the water level inside the reactor. The results were disappointing, as 2 days later Tepco reported that it was still not possible to obtain accurate data on the water level and pressure from Unit 2. The temperature near the containment vessel was reported to be very high which caused the new gauge to not function properly. One of the key issues mentioned was the evaporated water inside the tubes of the gauge.[39]

### Reactor stabilization

[edit]

By midday on 19 March grid power had been connected to the existing transformer at Unit 2 and work continued to connect the transformer to the new distribution panel installed in a nearby building.[40] Outside electricity became available at 15:46 JST on 20 March, but equipment still had to be repaired and reconnected.[41] On 24 March, electrical power (initially from temporary sources, but off-site power used from 3 April) was restored to parts of the unit which included the Main Control Room.[35][42] The IAEA reported temperatures on 27 March at the bottom of Unit 2's Reactor Pressure Vessel (RPV) fell from 100 °C (212 °F) to 97 °C (206.6 °F). While operators attempted to pump water from the turbine hall basement to the condenser, both of condensers turned out to be full.[43][44][45] Pumps were installed which moved up to 25 tons of condensed water per hour into on site storage tanks. This in turn freed up the needed storage condenser space for water in Unit 2's basement.[45] Ventilation systems were installed in Unit 2 on 11 June to clean the highly radioactive air encapsulated within the Reactor Building.[35]

On 28 June, TEPCO began injecting nitrogen into the containment vessel, which was expected to reduce the likelihood of further hydrogen explosions.[35]

Since 2 July, the Reactor has been cooled using fresh water treated by the on site water treatment plant.[35]

On 14 September at 11AM (JST) TEPCO began injecting water into the No. 2 reactor using the core spray system piping in addition to the feed water piping already being used as this method seemed to be effective in reducing the temperature in the No. 3 reactor. At that time the temperature at the bottom of the No. 2 reactor was still 114.4 degrees Celsius (237.92 °F), compared to the 84.9 °C degrees(184.82 °F) in the No.1 reactor and the 101.3 °C (214.34 °F) in the No. 3 reactor. The new method has led to some temperature decrease, but not as significant as the decrease that occurred in the No.3 reactor.[46]

After some positive effect was noticed using both the core spray system and feed water piping, TEPCO decided on 16 September to increase the amount of water pumped into the No. 2 reactor by one ton, in an attempt to further lower the temperature in the core, to a total of 7 tons per hour. The same was done for reactor No. 3, where 5 tons were added, bring the total to 12 tons per hour. TEPCO also added that the volume of cooling water into the No. 1 reactor would be increased as necessary.[47]

On 18 April 2011, remote control robot was used to enter the Reactor Building and performed a series of inspections.[48]

On 19 April 2011, TEPCO began transferring excess radioactive cooling water from the reactor's basement and maintenance tunnels to a waste processing facility.[49]

On 21 September 2011, Masanori Naitoh, director in charge of nuclear safety analysis at the Institute of Applied Energy, an expert commenting on the plan to contain the crisis at the Fukushima Daiichi nuclear plant, mentioned that the interior temperatures of the damaged reactors had to be checked to confirm cold-shutdown. Naitoh said that TEPCO was only measuring temperatures outside the reactors, and that the temperatures inside should be confirmed through simulation to confirm that they had fallen below 100 degrees, and that there were no risks of nuclear reactions recurring.[50]

In the first week of February 2012, temperatures inside reactor No. 2 became unstable. On 7 February, the amount of cooling water was increased from 10.5 tons to 13.5 tons per hour. After a slight initial decrease in temperature, sensor readings again showed the temperature rising at some locations in the bottom of the reactor. On 11 February, temperatures rose once again.[51][52][53][54] On 12 February, the temperature rose to 78.3 °C (172.94 °F). TEPCO denied the possibility of the core going critical again, because that would produce xenon, which was still below detectable levels. To prevent any possible nuclear criticality, TEPCO planned to dump boric acid into the reactor and to increase the volume of cooling water by 3 tons per hour.[55]

Since only one of the temperature-sensors showed fluctuating readings between 70 °C and 90 °C, TEPCO and NISA thought this sensor was malfunctioning. The sensor works on the principle of changing resistance between the surface of two different metals as the temperature changes. TEPCO planned measurements on this sensor.[vague] Since the radiation around reactor 2 could make it impossible to place new sensors inside the reactor vessel, the situation would become very serious if the other two sensors inside the reactor were to also fail. After that, it would be impossible to monitor the reactor. Kazuhiko Kudo, a professor of nuclear engineering at the university of Kyushu, Japan commented: "Because we haven't been able to grasp how the nuclear fuel in the cores has been distributed, it's impossible to rule out localized high temperature spots. As the high radiation rules out installing new temperature sensors, if the last two sensors fail, the situation will be much more serious indeed."[56][57][58] On 26 February, TEPCO sent a report to the Japanese government about the malfunctioning temperature-sensors and has since ceased monitoring that sensor. The other two temperature-sensors and the radiation levels inside the containment vessel would be used to monitor the state of the cold shutdown. The amount of cooling water would be lowered, after NISA's approval.[59]

On 15 April 2012, one of the two remaining temperature-sensors at the bottom of the No.2 reactor gave false readings, and because the electric resistance was found greatly increased, TEPCO concluded that it was broken, leaving only 18 of 36 temperature sensors still functioning. At 11 a.m., the remaining thermometer at this place measured 46.7 degrees Celsius.[60]

On 1 June 2012 TEPCO reported that another thermometer had malfunctioned, resulting in more than half of the temperature sensors, 23 out of 41, now being out of use in reactor No. 2., thus making it more problematic to monitor the state of "cold-shutdown". According to TEPCO, the high humidity in the reactor may be a contributing factor in the failure of the sensors. TEPCO stated that it is currently decontaminating the site and training workers to install new thermometers. The plan is to install new thermometers through pipes that are connected to the reactor. TEPCO stated that it plans to decontaminate the site and install the new thermometers by late July 2012.[61]

On 15 June 2012 TEPCO reported that a robot that was sent into the No. 2 reactor building on 13 June 2012 to take video images and radiation measurements, detected a reading of 880mSv (millisieverts) per hour of radiation on the fifth floor, which one floor (4.5 meters) directly above the reactor containment vessel. TEPCO suspects that during initial accident in March 2011, that radioactive substances leaked from the No. 2 reactor moved through the building, but after analyzing the images taken by the robot it could not find the exact route the radioactive substances traveled, and images taken by the robot found no major damage on the fifth floor. During the March 2011 nuclear accident the No. 2 reactor is believed to have released the largest amount of radioactive substances. But the overall route the radioactive material traveled has yet to be determined. TEPCO needs to find and repair the damaged parts of the reactor to recover melted nuclear fuel before TEPCO can begin the process of decommissioning the reactor. However high radiation often stops workers from entering the building. This scenario means it will take a long time to find the problems in the containment vessel.[62]

On 3 October 2012 TEPCO installed a new temperature-sensor inside reactor nr.2. The thermometer showed 42.6 degrees Celsius, another nearby the RPV bottom monitoring instrument (TE-2-3-69H3) indicated 46.1 degrees. At that moment only 1 out of the existing 5 sensors was functioning properly.[63] [64]

## Aftermath

[edit]

Radiation measurements from Fukushima Daiichi NPP, March 2011

### Pressure vessel damage

[edit]

On 15 May, TEPCO revealed that the pressure vessel that holds nuclear fuel "is likely to be damaged and leaking water at Units 2 and 3", which means most of the thousands of tons of water pumped into the reactors had leaked.[65]

### Containment damage

[edit]

On 27 March, TEPCO reported measurements of very high radiation levels, over 1000 mSv/h, in the basement of the Unit 2 turbine building, which officials reported was 10 million times higher than what would be found in the water of a normally functioning reactor. Hours into the media frenzy, the company retracted its report and stated that the figures were not credible.[66] "because the level was so high the worker taking the reading had to evacuate before confirming it with a second reading."[67] Shortly following the ensuing wave of media retractions that discredited the report worldwide, TEPCO clarified its initial retraction; the radiation from the pool surface in the basement of the Unit 2 turbine building was found to be "more than 1,000 millisieverts per hour", as originally reported, but the concentration of radioactive substances was 100,000 times higher than usual, not 10 million.[68]

### Possibility of re-criticality

[edit]

On 1 November 2011 TEPCO said that xenon-133 and xenon-135 were detected in gas-samples taken from the containment vessel of reactor 2, in a concentration of 6 to 10 (or more) parts per million becquerels per cubic centimeter. Xenon-135 was also detected in gas samples collected on 2 November. These isotopes are the result of nuclear fission-reaction of uranium. Because the short half-lives of these gases: (Xe-133: 5 days Xe-135: 9 hours), the presence could only mean that nuclear fissions were occurring at some places in the reactor. Boric-acid was poured into the reactor in an attempt to stop the fission-reactions. No significant change in temperature or pressure was found by TEPCO, so there was no sign of large-scale criticality. The reactor-cooling was continued, but TEPCO would examine the situation at reactor 1 and 3 also.[69][70][71][72] Professor Koji Okamoto of the University of Tokyo Graduate School made the comment that localized and temporary fission might still happen, and that the melted fuel could undergo fission, but the fuel was probably scattered around. Neutrons from radioactive materials could react with the uranium fuel and other substances. Self-sustaining chain reactions were unlikely, thanks to the huge amounts of boric acid that were poured into the reactor. According to Okamoto, these neutrons should be closely monitored to make sure fission did not happen, because when the fission-reactions were not controlled, it would be impossible to reach a state of "cold-shutdown". Therefore, it was needed to locate all molten fuel in and outside the reactor-vessel.[70][73]

On 3 November 2011 TEPCO said that the tiny amounts of xenon-135 detected in the reactor's containment vessel atmosphere came from spontaneous nuclear fission with curium-242 and curium-244, substances that were present in the nuclear fuel. A critical fission would have caused much higher concentrations of xenon isotopes. These reactions would occur constantly, and did not lead to criticality in the melted fuel of reactor 2. All assessments would be sent to NISA for reevaluation.[74][75][76]

The detection of xenon on the afternoon of 1 November by TEPCO was reported to NISA in the night. The next day, 2 November just past 7 a.m., NISA informed the Prime Minister Yoshihiko Noda's secretary about the possibility of critical reactions in reactor 2. Two hours later at 9 a.m. prime minister Edano learned the news. At a press-conference, the Chief Cabinet Secretary Osamu Fujimura revealed that Minister of Economy, Trade and Industry Yukio Edano sent a strong reprimand to Hiroyuki Fukano, the chief of NISA, because NISA failed to report the incident immediately to both himself and the Prime Minister's Office, and that NISA waited almost a day after the find was done. Fujimura said, "I have been told that NISA decided not to report the incident until the following morning because the agency didn't believe it was a dangerous situation."[77]

### Radioactive pollution of groundwater

[edit]

On 27 July 2013 was announced that extremely high levels of tritium and cesium were found in a pit containing about 5000 cubic meters of water on the seaside of the unit 2 reactor building. 8.7 million becquerels/liter Tritium was found and 2.35 billion becquerels/liter cesium. The NRA was concerned that leaks from this place could cause the high tritium levels in sea, and that there was still water flowing from the reactor into the turbine building into the pit. But TEPCO thought that this pollution was there from the first days in 2011, and stayed there. Nevertheless, TEPCO would control the site for leaks, and seal the soil around the pit.[78]

### 2017 Investigation of unit 2's containment in relation to elevated levels of radiation

[edit]

On 30 January, TEPCO inserted a camera into the unit 2 containment system to investigate the region underneath the reactor vessel.[79] TEPCO was able to estimate radiation levels of 530 Sv/hr, the highest level measured since the March 2011 accident when the previous high was measured at 73 Sv/hr.[80][81][82] This does not represent an increase in radiation at the reactor, but rather is the first measurement taken in the containment vessel at this location.[83] This investigation provided visual evidence that the core melt partially breached the reactor vessel.[84][85] A 1x1 meter hole in the grating of the undervessel Control Rod Drive inspection platform was identified along with various deposits of core debris and sediment.[86] TEPCO is using this information to help plan an upcoming robot entry to the under-vessel region of the concrete-floored containment.[85] These radiation levels are indicative of the presence of corium.[citation needed]

## See also

[edit]

* List of civilian nuclear accidents
* Lists of nuclear disasters and radioactive incidents
* Timeline of the Fukushima Daiichi nuclear disaster
* Comparison of Fukushima and Chernobyl nuclear accidents

## References

[edit]

1. ^ a b c d "Japan: Nuclear Power Reactors". Power Reactor Information System – PRIS. IAEA. Archived from the original on 28 May 2011. Retrieved 14 March 2011.
2. ^ "Japan's unfolding disaster 'bigger than Chernobyl'". The New Zealand Herald. 2 April 2011. Archived from the original on 30 March 2020. Retrieved 4 December 2012.
3. ^ "Explainer: What went wrong in Japan's nuclear reactors". IEEE Spectrum. 4 April 2011. Archived from the original on 21 August 2011.
4. ^ a b Black, Richard (15 March 2011). "Reactor breach worsens prospects". BBC Online. Archived from the original on 16 March 2011. Retrieved 23 March 2011.
5. ^ World Nuclear News (12 March 2011). "Battle to stabilise earthquake reactors". World Nuclear News. Retrieved 12 March 2011.
6. ^ "Press Release | Plant Status of Fukushima Daiichi Nuclear Power Station (as of 0 am 12 March)". TEPCO (Press release). 12 March 2011. Retrieved 23 March 2011.
7. ^ "Press Release | Plant Status of Fukushima Daiichi Nuclear Power Station (as of 11 pm 12 March)". TEPCO (Press release). 12 March 2011. Retrieved 23 March 2011.
8. ^ "Press Release | Plant Status of Fukushima Daiichi Nuclear Power Station (as of 0 pm 13 March)". TEPCO (Press release). 13 March 2011. Retrieved 23 March 2011.
9. ^ a b "IAEA Update on Japan Earthquake". Retrieved 16 March 2011. "As reported earlier, a 400 millisieverts (mSv) per hour radiation dose observed at Fukushima Daiichi occurred between 1s 3 and 4. This is a high dose-level value, but it is a local value at a single location and at a certain point in time. The IAEA continues to confirm the evolution and value of this dose rate .... because of this detected value, non-indispensable staff was evacuated from the plant, in line with the Emergency Response Plan, and that the population around the plant is already evacuated."
10. ^ "Press Release | Plant status of Fukushima Daiichi Nuclear Power Station (as of 8 pm 12 March)". TEPCO (Press release). 12 March 2011. Retrieved 23 March 2011.
11. ^ Broad, William J.; Tabuchi, Hiroko (14 March 2011). "In stricken fuel-cooling pools, a danger for the longer Term". The New York Times. Retrieved 14 March 2011.
12. ^ "TEPCO press release 3". Tepco (Press release). 14 March 2011.
13. ^ a b c d "Crisis continues at Fukushima nuclear plant as fuel rods exposed again". Kyodo News. Archived from the original on 20 March 2011. Retrieved 23 March 2011.
14. ^ "Seismic Damage Information (the 23rd Release)" (PDF). Nuclear and Industrial Safety Agency. 14 March 2011. Archived from the original (PDF) on 1 May 2011. Retrieved 12 April 2011.
15. ^ "Tepco Fears Fuel Rods Melt, Fights to Stabilize Stricken Reactor". Bloomberg BusinessWeek. 14 March 2011. Archived from the original on 16 March 2011. Retrieved 15 March 2011.
16. ^ "Fuel rods fully exposed again at Fukushima nuclear power plant". Xinhuanet. 14 March 2011. Archived from the original on 1 May 2011.
17. ^ Vastag, Brian (28 February 2011). "Nuclear crisis deepens as third reactor loses cooling capacity". The Washington Post. Retrieved 15 March 2011.
18. ^ Maugh II, Thomas H (14 March 2011). "Risk of meltdown increases at Japan nuclear reactor". Los Angeles Times. Retrieved 21 March 2011.
19. ^ "Tokyo Elec resumes work to pump water into No.2 reactor-Kyodo". Reuters. 14 March 2011. Archived from the original on 17 March 2011.
20. ^ TEPCO (10 August 2011) Chronology of Events at Fukushima Daiichi nuclear power station.
21. ^ Hiroko Tabuchi; Keith Bradsher; Matt Wald (14 March 2011). "Japan Faces Prospect of Nuclear Catastrophe as Workers Leave Plant". The New York Times.
22. ^ "Urgent: Blast heard at Fukushima's No.2 reactor: gov't; Kyodo News". english.kyodonews.jp. 2011. Archived from the original on 16 March 2011. Retrieved 14 March 2011. "The sound of a blast was heard Tuesday morning at the troubled No. 2 reactor of the quake-hit Fukushima No. 1 nuclear power plant, the government said. The incident occurred at 6:10 am and is feared to have damaged the reactor's pressure-suppression system, the Nuclear and Industrial Safety Agency said, citing a report from the plant's operator Tokyo Electric Power Co."
23. ^ "Japanese nuclear safety agency says explosion heard at Unit 2 of Fukushima Dai-ichi plant Canadian Business Online". canadianbusiness.com. 2011. Archived from the original on 29 April 2011. Retrieved 14 March 2011.
24. ^ "Blast heard at Fukushima's No.2 reactor: gov't". Archived from the original on 13 May 2011. Retrieved 14 March 2011. "Shortly after the 6:10 am incident, the radiation level exceeded the legal limit and reached 965.5 microsievert per hour (about 1 millisievert per hour), and it was feared that the reactor's pressure-suppression system was damaged, according to the Nuclear and Industrial Safety Agency. Tokyo Electric Power Co., the plant's operator, said it was evacuating workers from the plant, except for those necessary for the work to cool the reactor."
25. ^ Tabuchi, Hiroko; Sanger, David E.; Bradsher, Keith (14 March 2011). "Japan Faces Potential Nuclear Disaster as Radiation Levels Rise". The New York Times.
26. ^ "URGENT: Radiation shoots up at Fukushima nuke plant after blast heard". Kyodo News. Archived from the original on 13 May 2011. Retrieved 15 March 2011.
27. ^ NHK, 15 March 2011.
28. ^ "Japanese Government Warns that New Radiation Leak is Harmful to Health | Cleveland Leader". clevelandleader.com. 2011. Archived from the original on 28 April 2011. Retrieved 15 March 2011.
29. ^ 15 March 2011, Plant operator says reactor seal apparently not holed Archived 2 December 2012 at the Wayback Machine, Channel News Asia. Agence France-Presse.
30. ^ "UN atom chief sees possible Japan plant core damage". Reuters. 11 March 2011. Retrieved 15 March 2011.
31. ^ Hall, Kenji; Williams, Carol J. (27 February 2011). "Japan earthquake: Fire erupts again at Fukushima Daiichi reactor; nuclears rods damaged at other reactors". Los Angeles Times. Retrieved 18 March 2011.
32. ^ "Status report: Reactor-by-reactor at the Fukushima Daiichi plant". CNN. 24 March 2011. Retrieved 26 March 2011.
33. ^ "Air may be leaking from reactors No. 2 and 3". NHK WORLD English. 30 March 2011. Archived from the original on 11 May 2011. Retrieved 2 June 2011.
34. ^ "Inspection sheds light on Fukushima torus". World Nuclear Association. 24 April 2012.
35. ^ a b c d e "Records from March 11, 2011 to 31 July 2011" (PDF). TEPCO (Press release). Retrieved 22 August 2011.
36. ^ Sample, Ian (29 March 2011). "Japan may have lost race to save nuclear reactor". The Guardian. London. Retrieved 30 March 2011.
37. ^ TEPCO revises nuclear fuel damage ratios, NHK, 27 April 2011
38. ^ "Tepco confirms extra partial fuel rod meltdown at plant". BBC. 24 May 2011. Retrieved 27 May 2011.
39. ^ NHK-World (25 June 2011) TEPCO unable to gauge No.2 reactor water level Archived 30 December 2011 at the Wayback Machine
40. ^ "Press Release | Plant Status of Fukushima Daiichi Nuclear Power Station (as of 0:00 pm 19 Mar)". TEPCO (Press release). Retrieved 23 March 2011.
41. ^ "Seismic Damage Information (the 38th Release)" (PDF). Nuclear and Industrial Safety Agency. 21 March 2011. Archived from the original (PDF) on 9 April 2011. Retrieved 12 April 2011.
42. ^ "Seismic Damage Information (the 61st Release)" (PDF). Nuclear and Industrial Safety Agency. 29 March 2011. Archived from the original (PDF) on 1 May 2011. Retrieved 12 April 2011.
43. ^ "Fukushima Daiichi Nuclear Accident Update (27 March, 03:00 UTC)". International Atomic Energy Agency. 27 March 2011. Retrieved 27 March 2011.
44. ^ Staff (24 March 2007). "Official: Workers touched water with radiation 10,000 times normal". CNN Wire. Retrieved 27 March 2011.
45. ^ a b TEPCO halts work to remove radioactive water, NHK WORLD English (30 March 2011). Retrieved 30 April 2011.
46. ^ JAIF (15 September 2011) Earthquake report 205: TEPCO spraying water directly into No.2 reactor Archived 16 June 2013 at the Wayback Machine
47. ^ JAIF (16 September 2011) Earthquake report 207: TEPCO injects more water in two reactors Archived 19 April 2012 at the Wayback Machine
48. ^ "Information on Status of Nuclear Power Plants in Fukushima" (PDF). JAIF. Archived from the original (PDF) on 3 April 2012. Retrieved 22 August 2011.
49. ^ NHK, "Transfer of highly contaminated water begins", 19 April 2011.
50. ^ JAIF (21 September 2011) Earthquake-report 212: Expert urges checks of reactor interiors Archived 19 April 2012 at the Wayback Machine
51. ^ JAIF (NHK-world)(11 February 2012) Earthquake-report 345: Temperature inside No.2 reactor rises again
52. ^ The Mainichi Daily news( 8 February 2012) Fukushima No. 2 reactor cools slightly after increased water injection Archived 10 February 2012 at the Wayback Machine
53. ^ NHK-world (8 February 2012) Temperature decreasing inside Fukushima reactor[dead link]
54. ^ JAIF (7 February 2012) Earthquake report 340
55. ^ NHK-world (12 February 2012)Temperature rising at No.2 reactor Archived 27 November 2012 at the Wayback Machine
56. ^ The Mainichi Daily News (n) (13 February 2012)Possible sensor failure throws Fukushima reactor temp. data into doubt Archived 15 February 2012 at the Wayback Machine
57. ^ JAIF (13 February 2012)Earthquake report 346: TEPCO carefully monitoring No.2 reactor
58. ^ JAIF (13 February 2012)Earthquake report 346:One reading of Fukushima reactor exceeds 80 C
59. ^ TEPCO reports reactor thermometer problem to govt 16 February 2012 [dead link]
60. ^ The Japan Times (15 April 2012) Another thermometer breaks at Fukushima
61. ^ JAIF (4 June 2012) Earthquake-report 435: Thermometers malfunctioning at No.2 reactor Archived 18 June 2012 at the Wayback Machine
62. ^ JAIF (15 June 2012) Earthquake. report 444: High radiation one floor above reactor
63. ^ NHK-world (4 October 2012) Fukushima plant's reactor No.2 has new thermometer[permanent dead link]
64. ^ TEPCO (3 October 2012) Daily Report as of 4:00 PM, 3 October)
65. ^ Mitsuru Obe (16 May 2011). "Cores damaged at three reactors". The Wall Street Journal.
66. ^ Japanese nuclear firm admits error on radiation reading The Guardian, 27 March 2011.
67. ^ Worthington, Mark (27 March 2011). "Japan nuclear crisis: Radiation spike report 'mistaken'". BBC. Retrieved 27 March 2011.
68. ^ "Woes deepen over radioactive water at nuke plant, sea contamination". Kyodo News Network. 28 March 2011. Archived from the original on 27 March 2011. Retrieved 27 March 2011.
69. ^ NHK-world (2 November 2011) TEPCO: Reactor may have gone critical Archived 27 November 2012 at the Wayback Machine
70. ^ a b JAIF (2 November 2011) Earthquake-report 253  Archived 21 May 2013 at the Wayback Machine
71. ^ The Mainichi Daily News (2 November 2011) TEPCO finds sign of fresh nuclear fission at Fukushima reactor Archived 3 November 2011 at the Wayback Machine
72. ^ Businessweek (2 November 2011) Archived 31 July 2012 at archive.today
73. ^ NHK-world (2 November 2011) Xenon suggests possible nuclear fission Archived 4 April 2012 at the Wayback Machine
74. ^ NHK-world (3 November 2011) TEPCO retracts criticality call Archived 3 April 2012 at the Wayback Machine
75. ^ JAIF (3 November 2011)Earthquake-report 255 Archived 3 January 2012 at the Wayback Machine
76. ^ The Mainichi Daily News (4 November 2011) Xenon at Fukushima not result of 'critical' nuclear reactions: TEPCO Archived 5 November 2011 at the Wayback Machine
77. ^ The Mainichi Daily News (3 November 2011)Minister reprimands NISA chief for tardy reporting of xenon detection at Fukushima plant Archived 4 November 2011 at the Wayback Machine
78. ^ The Asahi Shimbun (28 July 2013) Extremely high tritium level found in water in pit at Fukushima plant Archived 1 August 2013 at the Wayback Machine
79. ^ Daley, Jason (6 February 2017). "Scientists Measure Highest Radiation Levels Yet Inside Fukushima's Damaged Reactors". Smithsonian.
80. ^ "Highest radiation reading since 3/11 detected at Fukushima No. 1 reactor". The Japan Times. 3 February 2017. Retrieved 4 February 2017.
81. ^ Peatland, william (3 February 2017). "Extreme Radiation Levels Detected At Fukushima Reactor, Highest Since 2011". Forbes. Retrieved 4 February 2017.
82. ^ "Record radiation level detected inside damaged Fukushima reactor". Japan Today. 3 February 2017. Archived from the original on 2 February 2017. Retrieved 4 February 2017.
83. ^ "Japanese nuclear plant just recorded an astronomical radiation level. Should we be worried?". The Washington Post. Retrieved 31 August 2018.
84. ^ "Investigation inside the pedestal for Unit 2 Primary Containment Vessel at Fukushima Daiichi Nuclear Power Station | TEPCO | TEPCO". www.tepco.co.jp. Retrieved 31 August 2018.
85. ^ a b http://www.tepco.co.jp/en/nu/fukushima-np/handouts/2017/images/handouts_170202_01-e.pdf [bare URL PDF]
86. ^ "Radiation level at Fukushima reactor highest since 2011 disaster; grating hole found - the Mainichi". Archived from the original on 6 February 2017. Retrieved 8 February 2017.

## External links

[edit]

* The Fukushima Nuclear Accident Independent Investigation Commission Report website in English
* Executive summary of the Fukushima Nuclear Accident Independent Investigation Commission Report
* Fukushima report: Key points in nuclear disaster report \- An outline of key quotes, findings and recommendations from the 88-page executive summary of the Nuclear Accident Independent Investigation Commission's report, as provided by the BBC, 5 July 2012
* Webcam Fukushima nuclear power plant I, Unit 1 through Unit 4
* Investigation Committee on the accidents at the Fukushima Nuclear Power Station of Tokyo Electric Power Company
* TEPCO News Releases, Tokyo Electric Power Company
* NISA Information update, Nuclear and Industrial Safety Agency, the nuclear safety authority of Japan
* JAIF Information update, Japan Atomic International Forum
* JAEA Information update, Japan Atomic Energy Agency
* IAEA Update on Japan Earthquake, International Atomic Energy Agency
* Nature Journal – Specials: Japan earthquake and nuclear crisis
* TerraFly Timeline Aerial Imagery of Fukushima Nuclear Reactor after 2011 Tsunami and Earthquake
* Documentary photographs: residential damage within "No Go" Zone
* In graphics: Fukushima nuclear alert, as provided by the BBC, 9 July 2012
* PreventionWeb Japan: 2011 Fukushima Daiichi nuclear disaster Archived 13 March 2013 at the Wayback Machine
* "What should we learn from the severe accident at the Fukushima Dai-ichi Nuclear Power Plant?" by Kenichi Ohmae, Team H2O Project. 28 October 2011

* v
* t
* e

2011 Tōhoku earthquake and tsunami

Nuclear
accidents|

| Power plants|

* Fukushima Daiichi nuclear disaster
* Unit 1
* Unit 2
* Unit 3
* Units 4-6
* Fukushima Daini plant
* Tōkai plant
* Onagawa plant
* Higashidori plant
* Rokkasho plant

|

Sequence of events|

* Timeline
* reactions
* International
* Japanese
* Radiation effects
* Leaks and dumping of radioactive water
* Aftermath

Topics|

* Okawa School tsunami tragedy
* Casualties
* Cleanup
* Fukushima 50
* Towns damaged
* Investigation
* National Diet
* Government
* Comparison
* Accident Rating

Movements|

* Project Sunshine for Japan
* Safecast
* Sayonara Nuclear Power Plants

Foreshocks,
Aftershocks|

* Sanriku, Japan (7.3, 9 March 2011)
* Miyagi, Japan (7.1, 7 April 2011)
* Fukushima, Japan (6.6, 11 April 2011)
* Miyagi, Japan (7.3, 7 December 2012)
* Fukushima, Japan (6.9, 22 November 2016)
* Fukushima, Japan (7.1, 13 February 2021)
* Miyagi, Japan (7.0, 20 March 2021)

Relief and
Recovery|

| Efforts|

* Humanitarian response
* Operation Pacific Assist
* Operation Tomodachi
* Reconstruction Agency
* Yuzuru Hanyu Notte Stellata

|

Fundraisers|

* Wrestling in Japan
* Hong Kong
* Taiwan

Pop culture|

* Films
* Documentaries
* Songs
* Manga
* Books
* TV drama

Other|

* Impact on video game industry
* No.18 Kyotoku-maru
* Tsunami fish
* Japan Trench Fast Drilling Project
* Ryou-Un Maru
* 869 Sanriku earthquake
* 2011 local elections
* Miracle Pine Tree
* Shinkansen Relay

* See also:  Japanese earthquakes
* Seismicity of the Sanriku coast
* List of tsunamis
* Nuclear power in Japan, section Seismicity
* Nuclear and radioactive incidents

*[v]: View this template
*[t]: Discuss this template
*[e]: Edit this template