Industrial Ethernet

Use of Ethernet in an industrial environment

Industrial Ethernet switch

Industrial Ethernet (IE) is the use of Ethernet in an industrial environment with protocols that provide determinism and real-time control.[1] Protocols for industrial Ethernet include EtherCAT, EtherNet/IP, PROFINET, POWERLINK, SERCOS III, CC-Link IE, and Modbus TCP.[1][2] Many industrial Ethernet protocols use a modified media access control (MAC) layer to provide low latency and determinism.[1] Some microprocessors provide industrial Ethernet support.

Industrial Ethernet can also refer to the use of standard Ethernet protocols with rugged connectors and extended temperature switches in an industrial environment, for automation or process control. Components used in plant process areas must be designed to work in harsh environments of temperature extremes, humidity, and vibration that exceed the ranges for information technology equipment intended for installation in controlled environments. The use of fiber-optic Ethernet variants reduces the problems of electrical noise and provides electrical isolation.

Some industrial networks emphasized deterministic delivery of transmitted data, whereas Ethernet used collision detection which made transport time for individual data packets difficult to estimate with increasing network traffic. Typically, industrial uses of Ethernet employ full-duplex standards and other methods so that collisions do not unacceptably influence transmission times.

## Application environment

[edit]

Industrial use requires consideration of the environment in which the equipment must operate. Factory equipment must tolerate a wider range of temperature, vibration, physical contamination and electrical noise than equipment installed in dedicated information-technology wiring closets. Since critical process control may rely on an Ethernet link, the economic cost of interruptions may be high and high availability is therefore an essential criterion. Industrial Ethernet networks must interoperate with both current and legacy systems, and must provide predictable performance and maintainability. In addition to physical compatibility and low-level transport protocols, a practical industrial Ethernet system must also provide interoperability of higher levels of the OSI model. An industrial network must provide security both from intrusions from outside the plant, and inadvertent or unauthorized use within the plant.[3]

When an industrial network must connect to an office network or external networks, a firewall system can be inserted to control exchange of data between the networks. This network separation preserves the performance and reliability of the industrial network.

Industrial environments are often much harsher, often subject to oil sprays, water sprays, and physical vibrations, so often industrial Ethernet requires a more rugged and watertight connector on one or both ends of the Cat 5 or Cat 6 cable, such as M12 connectors or M8 connectors, rather than the 8P8C connectors commonly used in homes and businesses.[4][5]

## Advantages and difficulties

[edit]

Programmable logic controllers (PLCs) communicate using one of several possible open or proprietary protocols, such as EtherNet/IP, EtherCAT, Modbus, Sinec H1, Profibus, CANopen, DeviceNet or FOUNDATION Fieldbus. The idea to use standard Ethernet makes these systems more interoperable.

Some of the advantages over other types of industrial network include:

* Increased speed, up from 9.6 kbit/s with RS-232 to 1 Gbit/s with Gigabit Ethernet
* Ability to use ubiquitous Cat5e/Cat6 cables
* Option to use optical fiber for increased distance
* Ability to use standard networking hardware for wired and wireless communication
* Ability to have more than two nodes on link, which was possible with RS-485 but not with RS-232
* Potential to use peer-to-peer architectures as opposed to client–server ones
* Better interoperability

Difficulties of using industrial Ethernet include:

* Migrating existing systems to a new protocol
* Real-time performance may suffer for protocols using TCP
* Additional complexity associated with network technology
* The minimum Ethernet frame size is 64 bytes, while typical industrial communication data sizes can be closer to 1–8 bytes. This protocol overhead affects data transmission efficiency.

## See also

[edit]

* Advanced Physical Layer
* Automotive Ethernet
* Computer network
* Distributed control system
* Fieldbus
* Human-machine interface
* Media Redundancy Protocol
* Modbus
* Parallel Redundancy Protocol
* Process control
* Programmable logic controller
* SCADA

## References

[edit]

1. ^ a b c Lin, Zihong (2018). An inside look at industrial Ethernet communication protocols (Rev. B) (PDF). Texas Instruments.
2. ^ Zurawski, Richard (2014). Industrial Communication Technology Handbook (Second ed.). CRC Press. ISBN 978-1482207323.
3. ^ Perry S. Marshall, John S. Rinaldi (2004). How to Plan, Install and Maintain TCP/IP Ethernet Networks. ISA. ISBN 1-55617-869-7. pp. 1–4.
4. ^ "Field Guide: Industrial Ethernet Connectivity". 2017.
5. ^ Dietmar Röring. "M12 versus RJ45 Ethernet connection systems". 2014.

## External links

[edit]

* Industrial Ethernet Advisory Group
* Lammermann.eu: Ethernet as a Real-Time Technology

* v
* t
* e

Ethernet family of local area network technologies

Speeds|

* 10 Mbit/s
* 100 Mbit/s
* 1 Gbit/s
* 2.5 and 5 Gbit/s
* 10 Gbit/s
* 25 and 50 Gbit/s
* 40 and 100 Gbit/s
* 200, 400, 800 and 1600 Gbit/s

General|

* Physical layer
* Autonegotiation
* EtherType
* Flow control
* Frames
* Jumbos

Organizations|

* IEEE 802.3
* Ethernet Alliance

Media|

* Fiber
* Twisted pair
* Coaxial
* First mile
* 10G-EPON

Historic|

* CSMA/CD
* StarLAN
* 10BROAD36
* 10BASE-FB
* 10BASE-FL
* 10BASE5
* 10BASE2
* MAU
* FOIRL
* 100BaseVG
* LattisNet
* Long Reach

Applications|

* Audio
* Automotive
* Carrier
* Data center
* Energy Efficiency
* Industrial
* Metro
* Power
* Synchronous

Transceivers|

* GBIC
* SFP/SFP+/QSFP/QSFP+/OSFP
* XENPAK/X2
* XFP
* CFP

Interfaces|

* AUI
* EAD
* MDI
* MII
* GMII
* XGMII
* XAUI

* Category
* Commons

* v
* t
* e

Automation protocols

Process automation|

* AS-i
* BSAP
* CC-Link Industrial Networks
* CIP
* CAN bus
* CANopen
* DeviceNet
* ControlNet
* DF-1
* DirectNET
* EtherCAT
* Ethernet Global Data (EGD)
* Ethernet Powerlink
* EtherNet/IP
* Factory Instrumentation Protocol
* FINS
* FOUNDATION fieldbus
* H1
* HSE
* GE SRTP
* HART Protocol
* Honeywell SDS
* HostLink
* INTERBUS
* IO-Link
* MECHATROLINK
* MelsecNet
* Modbus
* Optomux
* Process Image Exchange Protocol (PieP)
* PROFIBUS
* PROFINET
* RAPIEnet
* SERCOS interface
* SERCOS III
* Sinec H1
* SynqNet
* TTEthernet

Industrial control system|

* MTConnect
* OPC DA
* OPC HDA
* OPC UA

Building automation|

* 1-Wire
* BACnet
* BatiBUS
* C-Bus
* CEBus
* DALI
* DSI
* DyNet
* EnOcean
* EHS
* EIB
* FIP
* KNX
* LonTalk
* Modbus
* OpenTherm
* oBIX
* VSCP
* X10
* xAP
* xPL
* Z-Wave
* Zigbee

Power-system automation|

* IEC 60870
* IEC 60870-5
* IEC 60870-6
* DNP3
* Factory Instrumentation Protocol
* IEC 61850
* IEC 62351
* Modbus
* PROFIBUS

Automatic meter reading|

* ANSI C12.18
* IEC 61107
* DLMS/IEC 62056
* M-Bus
* Modbus
* Zigbee

Automobile / Vehicle|

* AFDX
* ARINC 429
* CAN bus
* ARINC 825
* SAE J1939
* NMEA 2000
* FMS
* Factory Instrumentation Protocol
* FlexRay
* IEBus
* J1587
* J1708
* Keyword Protocol 2000
* Unified Diagnostic Services
* LIN
* MOST
* SENT (SAE J2716)
* VAN
* Cyphal

*[v]: View this template
*[t]: Discuss this template
*[e]: Edit this template