Thermal mass

Use of thermal energy storage in building design

This article's lead section may be too short to adequately summarize the key points. Please consider expanding the lead to provide an accessible overview of all important aspects of the article. (July 2025)

|

Graph showing the effect of Heavy-weight and Light-weight constructions on the internal temperature of a naturally ventilated school classroom

In building design, thermal mass is a property of the matter of a building that requires a flow of heat in order for it to change temperature.

Not all writers agree on what physical property of matter "thermal mass" describes. Most writers use it as a synonym for heat capacity, the ability of a body to store thermal energy. It is typically referred to by the symbol Cth, and its SI unit is J/K or J/°C (which are equivalent).

Because:

* Christoph Reinhart at MIT describes thermal mass as its volume times its volumetric heat capacity. [1]

* Randa Ghattas, Franz-Joseph Ulm and Alison Ledwith, also at MIT, write that "It [thermal mass] is dependent on the relationship between the specific heat capacity, density, thickness and conductivity of a material" [2] although they don't provide a unit, describing materials only as "low" or "high" thermal mass.
* Chris Reardon equates thermal mass with volumetric heat capacity . [3]

The lack of a consistent definition of what property of matter thermal mass describes has led some writers to dismiss its use in building design as pseudoscience.[4][5][6]

## Background

[edit]

Main article: Heat capacity

The equation relating thermal energy to thermal mass is:

Q = C t h Δ T {\displaystyle Q=C_{\mathrm {th} }\Delta T\,}

where Q is the thermal energy transferred, Cth is the thermal mass of the body, and ΔT is the change in temperature.

For example, if 250 J of heat energy is added to a copper gear with a thermal mass of 38.46 J/°C, its temperature will rise by 6.50 °C. If the body consists of a homogeneous material with sufficiently known physical properties, the thermal mass is simply the mass of material present times the specific heat capacity of that material. For bodies made of many materials, the sum of heat capacities for their pure components may be used in the calculation, or in some cases (as for a whole animal, for example) the number may simply be measured for the entire body in question, directly.

As an extensive property, heat capacity is characteristic of an object; its corresponding intensive property is specific heat capacity, expressed in terms of a measure of the amount of material such as mass or number of moles, which must be multiplied by similar units to give the heat capacity of the entire body of material. Thus the heat capacity can be equivalently calculated as the product of the mass m of the body and the specific heat capacity c for the material, or the product of the number of moles of molecules present n and the molar specific heat capacity  c ¯ {\displaystyle {\bar {c}}} . For discussion of why the thermal energy storage abilities of pure substances vary, see factors that affect specific heat capacity.

For a body of uniform composition,  C t h {\displaystyle C_{\mathrm {th} }} can be approximated by

C t h = m c p {\displaystyle C_{\mathrm {th} }=mc_{\mathrm {p} }}

where  m {\displaystyle m} is the mass of the body and  c p {\displaystyle c_{\mathrm {p} }} is the isobaric specific heat capacity of the material averaged over temperature range in question. For bodies composed of numerous different materials, the thermal masses for the different components can just be added together.

## Heat capacity in buildings

[edit]

Christoph Reinhard describes the impact of heat capacity this way:[7]

>   * If the outside diurnal temperature swing frequently oscillates around a desired (balance point) temperature, adding thermal mass may increase the hours of comfort in a given time interval.
>   * Thermal mass may act as a liability to keep a space comfortable e.g. when it is only used intermittently.
>   * Thermal mass has really no effect if the direction of heat flow through the building envelope stays constant for extended periods of time.[verify]

Heat capacity is not normally calculated in the engineering of buildings. In the United States and Canada, national building codes and most state and local jurisdictions require that heating and cooling equipment be sized in accordance with Manual J[8] of the Air Conditioning Contractors of America. The Manual J process uses detailed measurements of a building's dimensions, construction, insulation, air-tightness, features and occupant loads, but it does not take into effect the heat capacity. Some heat capacity is presumed in the Manual J process, equipment sized according to Manual J is sized to maintain comfort at the first percentile of temperature for heating and the 99th percentile of temperature for cooling. The process presumes that the building has sufficient heat capacity to maintain comfort during brief excursions outside of those extremes.

### Construction examples

[edit]

* Earthship
* Rammed earth wall
* Trombe wall

## See also

[edit]

* Specific heat capacity
* Thermal energy storage
* Thermal inertia

## References

[edit]

1. ^ "4.401/4.464 Environmental Technologies in Buildings" (PDF).
2. ^ "Mapping Thermal Mass Benefit" (PDF).
3. ^ "Thermal mass | YourHome".
4. ^ "Thermal Mass and the Warming Climate". GreenBuildingAdvisor. 2022-07-21. Retrieved 2024-12-05.
5. ^ "Sizing HVAC System for ICF House". GreenBuildingAdvisor. 2022-07-17. Retrieved 2024-12-05.
6. ^ "Concrete, Thermal Mass, and Stable Ground Temps". GreenBuildingAdvisor. 2024-11-25. Retrieved 2024-12-05.
7. ^ Reinhard, Christoph (July 12, 2021). "4.401/4.464 Environmental Technologies in Buildings" (PDF). MIT.edu. Retrieved December 10, 2024.
8. ^ Manual J Residential Load Calculation. ACCA Technical Manuals. Air Conditioning Contractors of America. Archived from the original on 2024-09-07. Retrieved 2024-12-10.

* v
* t
* e

Heating, ventilation, and air conditioning

Fundamental
concepts|

* Air changes per hour (ACH)
* Bake-out
* Building envelope
* Convection
* Dilution
* Domestic energy consumption
* Enthalpy
* Fluid dynamics
* Gas compressor
* Heat pump and refrigeration cycle
* Heat transfer
* Humidity
* Infiltration
* Latent heat
* Noise control
* Outgassing
* Particulates
* Psychrometrics
* Sensible heat
* Stack effect
* Thermal comfort
* Thermal destratification
* Thermal mass
* Thermodynamics
* Vapour pressure of water

Technology|

* Absorption-compression heat pump
* Absorption refrigerator
* Air barrier
* Air conditioning
* Antifreeze
* Automobile air conditioning
* Autonomous building
* Building insulation materials
* Central heating
* Central solar heating
* Chilled beam
* Chilled water
* Constant air volume (CAV)
* Coolant
* Cross ventilation
* Dedicated outdoor air system (DOAS)
* Deep water source cooling
* Demand controlled ventilation (DCV)
* Displacement ventilation
* District cooling
* District heating
* Electric heating
* Energy recovery ventilation (ERV)
* Firestop
* Forced-air
* Forced-air gas
* Free cooling
* Heat recovery ventilation (HRV)
* Hybrid heat
* Hydronics
* Ice storage air conditioning
* Kitchen ventilation
* Mixed-mode ventilation
* Microgeneration
* Passive cooling
* Passive daytime radiative cooling
* Passive house
* Passive ventilation
* Radiant heating and cooling
* Radiant cooling
* Radiant heating
* Radon mitigation
* Refrigeration
* Renewable heat
* Room air distribution
* Solar air heat
* Solar combisystem
* Solar cooling
* Solar heating
* Thermal insulation
* Thermosiphon
* Underfloor air distribution
* Underfloor heating
* Vapor barrier
* Vapor-compression refrigeration (VCRS)
* Variable air volume (VAV)
* Variable refrigerant flow (VRF)
* Ventilation
* Water heat recycling

Components|

* Air conditioner inverter
* Air door
* Air filter
* Air handler
* Air ionizer
* Air-mixing plenum
* Air purifier
* Air source heat pump
* Attic fan
* Automatic balancing valve
* Back boiler
* Barrier pipe
* Blast damper
* Boiler
* Centrifugal fan
* Ceramic heater
* Chiller
* Condensate pump
* Condenser
* Condensing boiler
* Convection heater
* Compressor
* Cooling tower
* Damper
* Dehumidifier
* Duct
* Economizer
* Electrostatic precipitator
* Evaporative cooler
* Evaporator
* Exhaust hood
* Expansion tank
* Fan
* Fan coil unit
* Fan filter unit
* Fan heater
* Fire damper
* Fireplace
* Fireplace insert
* Freeze stat
* Flue
* Freon
* Fume hood
* Furnace
* Gas compressor
* Gas heater
* Gasoline heater
* Grease duct
* Grille
* Ground-coupled heat exchanger
* Ground source heat pump
* Heat exchanger
* Heat pipe
* Heat pump
* Heating film
* Heating system
* HEPA
* High efficiency glandless circulating pump
* High-pressure cut-off switch
* Humidifier
* Infrared heater
* Inverter compressor
* Kerosene heater
* Louver
* Mechanical room
* Oil heater
* Packaged terminal air conditioner
* Plenum space
* Pressurisation ductwork
* Process duct work
* Radiator
* Radiator reflector
* Recuperator
* Refrigerant
* Register
* Reversing valve
* Run-around coil
* Sail switch
* Scroll compressor
* Solar chimney
* Solar-assisted heat pump
* Space heater
* Smoke canopy
* Smoke damper
* Smoke exhaust ductwork
* Thermal expansion valve
* Thermal wheel
* Thermostatic radiator valve
* Trickle vent
* Trombe wall
* TurboSwing
* Turning vanes
* Ultra-low particulate air (ULPA)
* Whole-house fan
* Windcatcher
* Wood-burning stove
* Zone valve

Measurement
and control|

* Air flow meter
* Aquastat
* BACnet
* Blower door
* Building automation
* Carbon dioxide sensor
* Clean air delivery rate (CADR)
* Control valve
* Gas detector
* Home energy monitor
* Humidistat
* HVAC control system
* Infrared thermometer
* Intelligent buildings
* LonWorks
* Minimum efficiency reporting value (MERV)
* Normal temperature and pressure (NTP)
* OpenTherm
* Programmable communicating thermostat
* Programmable thermostat
* Psychrometrics
* Room temperature
* Smart thermostat
* Standard temperature and pressure (STP)
* Thermographic camera
* Thermostat
* Thermostatic radiator valve

Professions,
trades,
and services|

* Architectural acoustics
* Architectural engineering
* Architectural technologist
* Building services engineering
* Building information modeling (BIM)
* Deep energy retrofit
* Duct cleaning
* Duct leakage testing
* Environmental engineering
* Hydronic balancing
* Kitchen exhaust cleaning
* Mechanical engineering
* Mechanical, electrical, and plumbing
* Mold growth, assessment, and remediation
* Refrigerant reclamation
* Testing, adjusting, balancing

Industry
organizations|

* AHRI
* AMCA
* ASHRAE
* ASTM International
* BRE
* BSRIA
* CIBSE
* Institute of Refrigeration
* IIR
* LEED
* SMACNA
* UMC

Health and safety|

* Indoor air quality (IAQ)
* Passive smoking
* Sick building syndrome (SBS)
* Volatile organic compound (VOC)

See also|

* ASHRAE Handbook
* Building science
* Fireproofing
* Glossary of HVAC terms
* Warm Spaces
* World Refrigeration Day
* Template:Fire protection
* Template:Home automation
* Template:Solar energy

*[v]: View this template
*[t]: Discuss this template
*[e]: Edit this template